Figure 3–7: C30 VERTICAL SIDE MOUNTING REAR DIMENSIONS (STANDARD PANEL)
The relay, being modular in design, allows for the withdrawal and insertion of modules. Modules must only be replaced with
like modules in their original factory configured slots.
The enhanced faceplate can be opened to the left, once the thumb screw has been removed, as shown below. This allows
for easy accessibility of the modules for withdrawal. The new wide-angle hinge assembly in the enhanced front panel opens
completely and allows easy access to all modules in the C30.
Module withdrawal and insertion may only be performed when control power has been
removed from the unit. Inserting an incorrect module type into a slot may result in personal
injury, damage to the unit or connected equipment, or undesired operation!
Proper electrostatic discharge protection (for example, a static strap) must be used when
coming in contact with modules while the relay is energized!
C30 Controller System
3.1.2 MODULE WITHDRAWAL AND INSERTION