1 GETTING STARTED
Select the "UR" device from the EnerVista Launchpad to start EnerVista UR Setup.
Click the Quick Connect button to open the Quick Connect dialog box.
Select the Ethernet interface and enter the IP address assigned to the C30, then click Connect.
The EnerVista UR Setup software will create a site named "Quick Connect" with a corresponding device also named
"Quick Connect" and display them on the upper-left corner of the screen. Expand the sections to view data directly
from the C30 device.
Each time the EnerVista UR Setup software is initialized, click the Quick Connect button to establish direct communica-
tions to the C30. This ensures that configuration of the EnerVista UR Setup software matches the C30 model number.
When direct communications with the C30 via Ethernet is complete, make the following changes:
From the Windows desktop, right-click the My Network Places icon and select Properties to open the network con-
Right-click the Local Area Connection icon and select the Properties item.
Select the Internet Protocol (TCP/IP) item from the list provided and click the Properties button.
Set the computer to "Obtain a relay address automatically" as shown below.
If this computer is used to connect to the Internet, re-enable any proxy server settings after the laptop has been discon-
nected from the C30 relay.
AUTOMATIC DISCOVERY OF ETHERNET DEVICES
The EnerVista UR Setup software can automatically discover and communicate to all UR-series IEDs located on an Ether-
Using the Quick Connect feature, a single click of the mouse will trigger the software to automatically detect any UR-series
relays located on the network. The EnerVista UR Setup software will then proceed to configure all settings and order code
options in the Device Setup menu, for the purpose of communicating to multiple relays. This feature allows the user to
identify and interrogate, in seconds, all UR-series devices in a particular location.
1.3 ENERVISTA UR SETUP SOFTWARE
C30 Controller System