6.1 Safety precautions
The machine is adaptive in following situation
1. Applicable ambient temperature range:
2. If the supply cord is damaged, it must be replaced by the manufacturer or its service agent or a similar qualified
3. If the fuse on the indoor PC board is broken please change it with the type.
4. The wiring method should be in line with the local wiring standard.
5. The power cable should be:
H05RN-F 3G 4.0mm
(outdoor unit 1UH071/090/105N1ERG),
or H05RN-F 3G 6.0mm
or H05RN-F 5G 4.0mm
or H05RN-F 5G 6.0mm
The connecting cable should be:
All the cables shall have got the European authentication certificate. During installation, when the connecting cables
break off, it must be assured that the grounding wire is the last one to be broken off.
6. The power cable and connect cable should be self provided.
7. The breaker of the air conditioner should be all pole switch, and the distance between its two contacts should be
no less than 3mm.
8. The indoor unit installation height is at least 2.5m.
9. A leakage breaker must be installed.
10.1 For ADH105H1ERG, ADH125H1ERG, ADH140H1ERG, ADH160H1ERG, ADH200H1ERG,
ADH250H1ERG, static pressure selection need achieved by wired controller, refer wired controller's manual to get
(outdoor unit 1UH125/140/160P1ERG),
(outdoor unit 1UH125/140P1EK)
(outdoor unit 1UH200/250W1ERK);