Connect the communication connector configured for the inverter to the RS485 terminal of the inverter as
shown in Figure 32C below.
Connect the communication connector pinout and the user´s device according to Table 22 above. Make sure
the connection is correct.
6.2 Optional communication
If you need further information on optional communication possibilities, please contact the AEG technical service.
Optional communication modes include Ethernet, which also needs corresponding communication parts and compo-
nents. All operation parameters of the inverter will be transferred through RS485 port, and then to the communication
devices. These allow the transfer of the monitoring data to the monitoring system (Web Portal / App).
6.3 AEG WiFi200 (AEG WiFi Stick) communication module
6.3.1 AEG WiFi Stick product overview
The AEG WiFi200 communication module (hereinafter referred to as "AEG WiFi Stick") is a device enabling the trans-
mission of relevant performance data from your AEG inverter to the monitoring software (AEG InverterControl App and
AEG InverterControl Monitoring Webportal). It allows users to configure inverter parameters, and control and monitor the
inverter locally and remotely. The WiFi Stick fits the RS485 port of the AEG inverters.
WiFi is the standard communication mode for AS-IC01-2. The AEG WiFi Stick features one RS485 and one WiFi commu-
nication port for the data transmission. The AEG WiFi Stick features a general serial port which meets the network stand-
ards and has built-in TCP/IP protocol stack for the transformation between the user serial port and WiFi port.
Below is an overview of the AEG WiFi Stick features:
PD201808 AEG GRID-TIED THREE-PHASE SOLAR INVERTER (12-30 kW) V.2-18 EN
Figure 32C: Communication cable connection
Automatic control of data flow, automatic identification and transmission
direction of control data and no handshake signal is needed
Transmission speed 300~115200 Baud
Up to 32 devices of RS485
the maximum transmission distance 1200m