Ensure that the voltage meets the requirement mentioned in the technical parameters section (2.4);
6. Ensure that all electrical safety indications are clearly identifiable at the installation site.
4.2 Grid-tied operation
The following section describes the detailed operation of the inverter, covering the inspection before operation, grid-
Please start the inverter as follows:
Ensure the requirements mentioned in section 4.1 are met;
Switch on the breakers at the AC side;
Switch on the integrated DC switch;
4. Switch on the switch on the DC side;
Observe the LED indicators and information displayed on the screen. Refer to chapter 5 for detailed
Green indicator blinks, others off: the inverter is power on and in self-inspection;
Green indicator on, others off: the inverter is generating power after self-inspection;
"Warn" or "Fault" indicators are on or blinking: the inverter is power on, but faults are occurring. Please refer to
section 5.3 for detailed information, and then stop operation as explained in section 4.3; finally, solve the problems
as referred to in chapter 7. If all faults are solved, follow the indications in chapter 4.
PD201808 AEG GRID-TIED THREE-PHASE SOLAR INVERTER (12-30 kW) V.2-18 EN
In order to ensure a safe, smooth and stable operation of the PV power generation system,
all the newly installed / renovated / repaired components of the plant and
the grid-connected inverters must undergo inspection before operation start.
When the inverter is powered for the first time, please refer to section 5.5
for grid certification choice. Keep the inverter turned on at least 30 minutes to
allow for charging of the internal clock battery.