Failure to follow these instructions may lead to death, serious injury or property
Any electrical wiring required to install this device shall conform to applicable codes
and standards (ANSI/NFPA 70). A qualified electrician is recommended to perform
To reduce the risk of electric shock, never service, install or uninstall this device from
service while energized.
This equipment has arcing or sparking parts that should not be exposed to flammable
vapors. This equipment should be located at least 18 inches above the floor.
This device is equipped with an auto reset feature
This device should be supervised when used around children.
Do not put fingers into the electric vehicle connector.
Do not use this product if the flexible power cord or EV cable is frayed, has broken
insulation, or any other signs of damage.
Do not use this product if the enclosure or the EV connector is broken, cracked, open,
or shows any other indication of damage.
A torque driver shall be used to make power connections to ensure that adequate
contact pressure is applied. See the installation section of this manual for additional
A device provided with a wire connector for field installed wiring shall be provided with
instructions specifying that the connector provided shall be used in making the field
When installing this device in the hard wired configuration, power connections shall be
made at line terminals with 14.5in.-lbs. torque.
An insulated grounding conductor that is identical in size, insulation material, and
thickness to the grounded and ungrounded branch-circuit supply conductors, except
that it is green with or without one or more yellow stripes, shall be installed as part of
the branch circuit that supplies the device or system.
The grounding conductor shall be grounded to earth at the service equipment or, when
supplied by a separately derived system, at the supply transformer.
Do not attempt to operate this device if the ambient temperature is greater than
Use 6-8 AWG, 75C copper wire to connect to supply circuit.
CAUTION: To reduce the risk of fire, connect only to a circuit provided with 40 amperes
maximum branch circuit overcurrent protection in accordance with the ANSI/NFPA 70
National Electrical Code.
1.7 Code and Standard References
This device has been designated to meet the requirements in section 626 of the
National Electric Code (NEC®).
UL Listing with Listing Number – Siemens VersiCharge Devices are listed in UL file #
Complies with the following UL Standards: 2594, 2231-1, 2231-2
EV interface compliant to SAE J-1772 Level II
This equipment has been tested and found to comply with the limits for a Class B
digital device, pursuant to part 15 of the FCC Rules. These limits are designed to
provide reasonable protection against harmful interference in a residential
installation. This equipment generates, uses and can radiate radio frequency energy
and, if not installed and used in accordance with the instructions, may cause harmful
interference to radio communications. However, there is no guarantee that
If this device is connected to a vehicle at the time that power is restored
following an outage, charging may automatically resume.
If this device is connected to a vehicle and a ground fault trip occurs, charging
may automatically resume after a delay period.