duCT mounT InsTallaTIon
Position template sticker on supply duct. For tall coils that do not have this
clearance available, refer to remote mounting instructions.
Secure bracket to duct using #8
self-drilling sheet metal screws (4).
Proceed to page 13 for plumbing and wiring instructions.
Drill 1-3/4-in. hole.
A) Slide foam gasket over nozzle and
insert the nozzle into duct hole
B) Push down to secure humidifier to
bracket arms. Ensure gasket forms
tight seal in duct hole.
Allow 3 in. clear-
ance from nozzle
outlet to duct wall.