Steam installation: Continued
Since a steam hose (pressure hose) is used on
the last section before the steam calorifier con-
nection branch, it is important to ensure a contin-
uous slope all the way, see fig. 2.
The hose should not be allowed to sag, see fig.
3, since this would create local accumulations of
condensate, leading to a risk of water shock in
the steam battery.
Since hoses are used after the battery, a continu-
ous slope must also here be ensured all the way
to the water discharger.
All pipes should be insulated to reduce the risk of
burns, while also reducing the heat loss to the
Water steam (Operating steam pressure)
1 - 10 bar absolute pressure
Installation - steam heating
487 18 39 01 - 300/500/750 - GB