Installation - steam heating
From the main steam pipe (flow) the steam
is tapped through a service line at the top
(A) (the tap-off point is at the top to prevent
condensate in the steam).
Bring the service line down to the same
height (or slightly above) the top steam con-
nection (B) of the steam batterir.
Install a stop cock (slide valve) (C) and a dirt
collector (D) before the steam battery.
Mount the included inlet and outlet hoses (E)
on the battery. To prevent the inlet and outlet
connecting branches from being deformed, it
is important to support them using an extra
Then connect the steam installation to the
other end of the steam hoses (E) using the
accompanying counter flanges (F).
Just after the outlet flange (F), mount a dirt
After the dirt collector, place a mechanical
water discharger (G) (a thermal water dis-
charger is unsuited for a battery of this size)
and a manual stop cock (C). A return line
then takes the condensate back to the main
To be continued
487 18 39 01 - 300/500/750 - GB