1. Apply input power to the mains transformer.
2. Check that the Auxiliary Voltage at terminals AUX + and AUX – on the main
terminal strip measures between 13.5 V and 14 V d.c. If the auxiliary voltage
is under 13.5 V too much current is being drawn. For the current consumption
of the control panel and keypads see
3. If the auxiliary voltage is between 13.5 V and 14 V d.c. connect the battery to
the Battery Terminals, observing the correct polarity.
Further Test Procedure
Once the control panel has been installed, and the power up and initial test procedure
have been performed, it is advisable to check the keypad(s) and ancillary devices are
To test the keypad:
• Press 1234 1
(Escape) – Panel Escapes from the setting routine.
This ensures that the keypad and control are communicating with each other cor-
rectly. Test each keypad in this manner.
To test the detectors see
Testing the Alarm System 
Wiring the Zones
The zone terminals should be connected to a normally closed contact. Unused zones
should be shorted across the terminal using the zone links provided.
– Panel starts to Set.
Section 4: OPERATING THE ACCORD SECURITY SYSTEM;