mounting the unit
Push the optional board from behind into the opening on the front cover
) until the position of the 64-pole system connector on the main
board corresponds with the position of the socket.
Insert the optional board from the right onto the 64-pole system
connector on the main board (
Screw the optional board tight at the fastening points in the front section
of the optional board (
Installing the optional board
Close the right-hand side wall of the unit as follows
♦ Insert the right-hand side wall from above into the guide on the front
♦ Swing back the side wall.
♦ Screw the side wall tight again by means of the two fixing screws.
Mount the unit as follows:
♦ Insert the unit into its mounting position from the front underneath
the DC link bus module.
♦ Lift the unit upwards until the DC link bus module is completely in its
original position again.
♦ Screw the unit tight to the mounting surface with the fixing screws.
♦ Interlock the DC bus module.
♦ Re-connect all previously removed connecting cables.
♦ Check all connecting cables and the shield to make sure they sit
properly and are in the correct position.
♦ To designate the optional board, insert the relevant designation
plate into the envisaged position on the front of the unit.
♦ After powering up the voltage, you can log on the optional boards in
the software of the unit and commence start-up.
). The view shows the installed state.