Establishing the link
Dimensions and drilling plan
Siemens Schweiz AG
Radio repeater AVS14.390
• To establish the radio link, the device must be temporarily connected to power prior
to mounting, enabling the radio link to be opened and tested
• The radio repeater must be fitted inside the building
Power is supplied via the enclosed power pack. The wires are interchangeable.
Establish the radio link in the vicinity of the radio module prior to mounting so that all
system components are within easy reach.
Prerequisite for the radio link is that all components receive power, which means that
the radio module must be correctly connected to the basic unit and power must be
correctly supplied to the radio repeater.
Press the button on the radio module for at least 8
seconds until the LED on the radio module starts
flashing at high frequency.
Press the button on the installed radio repeater until
the LED starts flashing at high frequency.
The link is established when the LED on the radio
The test is made to check the quality of the radio link.
• The test can be stopped by pressing the ESC button
• While the radio link can be opened on the boiler, the test should be made at the
location where the room unit will be installed
Press button 3 on the radio repeater for a maximum of 8 seconds until the LED
starts flashing at low frequency.
When radio communication works, the LED on the radio module flashes briefly at
After the test, press the button on the radio repeater again briefly until the LED
Mounting and installation
22. November 2006