The following functions they are used during
commissioning of the system and are
documented here for reference.
The loop status function shows the status
of the loop circuit, for example if it is running
or has stopped. A running loop implies the
loop is operating correctly and requires no
intervention, however a stopped loop must be
started, using the start detection function.
The display also shows the number of
devices connected to the loop and the
address of the last device on the loop.
The local input function configures two
terminals at the panel, the terminals can be
used for Class change, Fire input or Evacuate
input application. If used as a Fire input it is
possible to set the input in test mode, similar
to putting a zone in test mode.
The display also shows if the input is
enabled or disabled.
A loop map function provides a list of
devices on the loop in consecutive order, as
installed on the circuit. Starting at end-1
terminals of the loop finishing at the end-2.
Devices on the loop can include detectors,
manual call points and transponder units.
The list also shows the label given to each
796689 (4188-658) i2__04/07