To put a zone in and
out of test mode
Press select to change to a required
Press to select In Test field [ ]
796689 (4188-658) i2_04/07
Any zone can be put into test mode to allow
the devices in the zone to be tested. In test
mode, the panel will not detect fires from
devices within the zone in test. An active
manual call point or detector in the zone will
cause master alarms to sound for a short
duration and the device is reset thereafter.
On completion of the test it is important to
exit the test mode to resume normal operation
for that zone.
Enter access level 2 (A2) and use the
navigation buttons to highlight and
If a zone is put into test mode the panel
will see the zone fire events as test fires.
Press select to toggle NO/YES
Select NO to take zone out of test
or YES to put the zone in test
When a zone is in the test mode and a
device in the zone is put into fire condition,
the alarms will sound for a short duration
and the device is reset thereafter.
Press to select a [Zone] field