796689 (4188-658) i2_04/07
operation and meaning
STEADY – There is either a mains
or battery supply fault.
OFF – There is no power fault.
STEADY – There is a fire routing
OFF – There is no FRE fault.
STEADY – There is a sounder
circuit open or short circuit fault.
OFF – There is no sounder circuit
STEADY – There is at least one
disablement or the panel is in
engineering mode, view the
disablement log for details, see
The engineering mode is
normally only accessed by the
OFF – There are no disablements.
STEADY – The fire routing
equipment (FRE) is disabled.
OFF – The FRE is not disabled.
STEADY – The system alarm
sounders are disabled.
OFF – The system alarm sounders
are not disabled.
STEADY – The panel or Zone is in
OFF – The panel or zone is not in