The Delay Mode (also called Day mode)
facility allows the panel to delay the fire
alarms from sounding in the event of a fire.
With the Delay mode active there is an initial
30 seconds (factory set) delay before alarms
are made active in the event of a fire. The
factory set initial delay time can be changed
to a different value, see page 32.
Enter access level 2.
Press Delay button to activate Delay
mode facility for a pre-configured time of
up to 8 hours.
During a fire condition whilst the initial delay
is operating it is possible to activate further a
pre-configured alarm delay of up to
10 minutes on pressing the Verify button,
see page 13.
The delay mode is only operable if
the function is configured for
operation during service and
If timeout is not pre-configured
then the Delay function is
796689 (4188-658) i2__04/07