Installing the Device
2.5 Connecting the Failsafe Alarm Relay
Connecting the Failsafe Alarm Relay
The failsafe relay can be configured to latch based on alarm conditions. The NO
(Normally Open) contact is closed when the unit is powered and there are no active
alarms. If the device is not powered or if an active alarm is configured, the relay
opens the NO contact and closes the NC (Normally Closed) contact.
Control of the failsafe relay output is configurable through RUGGEDCOM RSG909R .
One common application for this relay is to signal an alarm if a power failure occurs.
For more information, refer to the RUGGEDCOM ROS Configuration Manual for the
Place the device against the panel and align the adapters with the mounting
Screw (M5 or #10-24)
Panel Mount Adapter
Secure the adapters to the panel with M5 or #10-24 screws.
Installation Manual, 02/2021, C79000-G8976-1388-12