Precautions When Using the BACnet
Please read and agree to the LICENSE AGREEMENT FOR "BACnet
of this manual before using the BACnet
Please confirm that the PC for the BACnet
Specifications" described in the Appendix of this manual.
Please read and fully understand this manual before using the BACnet
Be careful not to shutdown or turn off the power supply of the PC or unplug its transmission adap-
tor. Do not terminate the BACnet
eration of the BACnet
To ensure continuous normal operation of this software,set the PC so that it would not go into an
energy saving mode such as standby mode, sleep mode or execute hibernation. If the PC goes
into a standby, sleep mode or execute hibernation, this software may not function properly. The
method for releasing the energy saving or hibernation of the PC depends on the Windows ver-
sions. For windows
icon to select "Change power settings". Check "Power saver" in the "Preferred plans" and select
"Change plan settings" to set "Never".
The CD for this software and the software protection key (WIBU-KEY) will not be reissued. Keep
and handle them with great care after installing.
Gateway programs perform schedules, operation recording and electricity apportion-
ment data control based on date and time set in the personal computer. Adjust date and time pe-
riodically and by a small amount. Changing date and time may affect the functions listed above.
When the date/time of the PC running BACnet
collected for the electricity charge apportionment for that period will be deleted and be newly col-
lected. When the date/time is adjusted to roll forward in time, there will be no data for that period.
Such cases will result in incorrect calculation results for the electricity charge apportionment so
the user should be careful when adjusting date/time for the PC.
When program execution environment of Windows
is installed or running on the same PC, operation of BACnet
may not install or run properly. It is usually extremely difficult to detect such conditions, if it oc-
curs. It is recommended that BACnet
Gateway product is provided with software, drivers, components listed below. If the
same kind of software, drivers, components with different version is installed on the same PC,
Gateway may not install or run properly.
OpenLDV (U10 USB Network Interface driver)
Visual C++ 2005 SP1 Redistributable
Gateway program unless necessary. Otherwise, normal op-
Gateway may not be performed.
7, right click the desktop to select "Personalize" and click "Screen Saver"
Gateway be installed on a new PC, dedicated for the use
Copyright© 2010, 2011 Fujitsu General Limited. All rights reserved.
Gateway meets the operating condition of the "Product
Gateway is adjusted to roll back in time, the data
is corrupted or abnormal, or if other software
Gateway may be interfered and
Gateway" at the beginning