Scans by the network and detects and registers usable R.C. groups and outdoor units.
The units registered by scanning are managed by BACnet
When you want to reset "Unit Registration", open the "Unit Registration" screen.
Select the menu items in order of "Setting"→"Unit Registration" from the Menu bar.
Set the scan Targets.
Selects the name of the adaptor which is to perform scanning.
(Name set at par. 6-5 "Adaptor Setting")
Unit Registration is necessary for each adaptor.
When an adapter is set at a blank line, a blank line is added below it.
The same adapter can be set on multiple lines and different refrigerant system can also be
Specifies by checkbox whether or not secure registration is to be performed when scanning
Checked: Secure registration (Recommended) Not checked: No secure registration
When scanning is performed by secure registration, operation of the units is stopped.
When you do not want to stop operation, uncheck the checkbox.
See par. 11-1 No.4.
Copyright© 2010, 2011 Fujitsu General Limited. All rights reserved.
When partially scanning, specify the start number of the refrigerant system by pull-
down menu or key input. See par.11-1 No.8.
When partially scanning, specify the end number of the refrigerant system by pull-
down menu or key input.
Displays the name of the device used by the relevant network.
Displays the status of the device used by the relevant network.
Normal: "Ready" Abnormal: "Error" Not connected: "Blank"
When the (a) "Wink" button is clicked, the SVC lamp of the Transmission adaptor
used by the relevant network lights (for approx. 2 second) and connection of the se-
lected adaptor can be identified. (Effective only when the status of the Transmission
adaptor is normal.)