Combustion Air Pipe for details concerning the conversion
to the alternate vent/flue and combustion air connections.
When using the horizontal alternate vent configuration,
you must use the RF000142 vent drain kit. See following
Alternate Vent/Flue Location
Recommended Installation Positions
Alternate Electrical and Gas Line Connections
This furnace has provisions allowing for electrical and gas line
connections through either side panel. In horizontal applica-
tions the connections can be made either through the "top" or
"bottom" of the furnace.
A drain pan must be provided if the furnace is installed above
a conditioned area. The drain pan must cover the entire area
under the furnace (and air conditioning coil if applicable).
Refer to Horizontal Applications and Conditions - Drain
Trap and Lines.
OSSIBLE PROPERTY DAMAGE
OCCUR IF THE CORRECT CONVERSION KITS ARE NOT INSTALLED
APPROPRIATE KITS MUST BE APPLIED TO ENSURE SAFE AND PROPER
LL CONVERSIONS MUST BE PERFORMED BY A
QUALIFIED INSTALLER OR SERVICE AGENCY
LPM-07* supports both Honeywell and White-Rodgers 1-stage valves
In Canada, gas furnaces are only certified to 4500 feet.
Propane Gas/High Altitude Installations
This furnace is shipped from the factory configured for natural
gas at standard altitude. Propane gas installations require an
orifice and spring change to compensate for the energy con-
tent difference between natural and propane gas.
High altitude installations may require both a pressure
switch and an orifice/spring change. These changes are
necessary to compensate for the natural reduction in the
density of both the gas fuel and the combustion air at
Installation of this furnace at altitudes above 7000 ft (2134
m), shall be made in accordance with the Listed High Alti-
tude Conversion Kit available with this furnace.
For furnaces being converted to LP gas, it is strongly rec-
ommended that a LPLP03 kit also be installed. The use of
this kit will prevent the furnace from firing when the LP gas
supply pressure is too low to support proper combustion.
Contact the distributor for a tabular listing of appropriate
manufacturer's kits for propane gas and/or high altitude
installations. The indicated kits must be used to insure
safe and proper furnace operation. All conversions must
be performed by a qualified installer, or service agency.
PERSONAL INJURY OR DEATH MAY
1.25mm 10.0" w.c. 6.0" w.c.