10. Pump may be running too slowly; check voltage at
motor terminals and at meter while pump is running.
If low, see wiring instructions or consult power
company. Check for loose connections.
11. Pump may be too hot.
A. Check line voltage; if less than 90% or more
than 110% of rated voltage consult a licensed
B. Increase ventilation.
C. Reduce ambient temperature.
D. Tighten any loose connections.
MECHANICAL TROUBLES AND NOISE
1. If suction and discharge piping are not adequately
supported, pump assembly will be strained. See
"Installation", Page 3.
2. Do not mount pump on a wooden platform!
Securely mount on concrete platform for quietest
Can shock, burn,
or cause death.
on pump or motor.