Health ﬁ lter.............................20 WE’RE THINKING OF YOU Thank you for purchasing an Electrolux appliance. You’ve chosen a product that brings with it decades of professional experience and innovation. Ingenious and stylish, it has been designed with you in mind. So whenever you use it, you can be safe in the knowledge that you’ll get great results every time.
www.electroluxaircomfort.com 3 SAFETY PRECAUTIONS • Read the manual carefully before operation. • Make sure that the unit is properly grounded to prevent electric shock. • Keep the manual for further reference. • Do not attempt to repair the unit yourself to •...
4 www.electroluxaircomfort.com DESCRIPTION 1 Indoor unit 2 Air inlet (indoor unit) 3 Air outlet (indoor unit) 4 Outdoor unit 5 Air inlet (outdoor unit) 6 Air outlet (outdoor unit) 7 Mains cord 8 Remote control 9 Front panel 10 Filter 11 Horizontal louvre 12 Wall pipe 13 Binding tape...
www.electroluxaircomfort.com 5 Explanation of buttons Button Explanation ON/OFF Press the button to switch on the unit. Press the button again to switch off the unit. MODE Press the button to set the operation mode: AUTO, COOL, DRY, FAN and HEAT. Default setting: AUTO. In the AUTO mode, the temperature is not shown.
6 www.electroluxaircomfort.com Button Explanation TIMER ON Press the button to set the timer function for switching on the unit. If the TIMER ON symbol blinks, press the UP or DOWN button to set the time. Keep the button pressed for two seconds to accelerate the process.
www.electroluxaircomfort.com 7 Button Explanation If you set a temperature of 21-27 °C, the temperature will decrease by 1 °C every hour. After 2 °C, the temperature will be maintained. If you set a temperature of 28-30 °C, the temperature will decrease by 1 °C every hour.
8 www.electroluxaircomfort.com 8 °C heating function • If the remote control transmits a signal, the In HEAT mode, simultaneously press the ION- transmitting symbol will blink for 1 second. FILTER button and the CLOCK button to enable The bell will ring if the main unit receives the or disable the 8 °C heating function.
www.electroluxaircomfort.com 9 CLEANING AND MAINTENANCE WARNING • Before cleaning and maintenance, disconnect the unit from the power supply. • Do not immerse the unit in water or other liquids. If the unit is immersed in water or other liquids, do not remove the unit with your hands.
10 www.electroluxaircomfort.com TROUBLESHOOTING CAUTION • The unit is not user-serviceable. Do not The following checks can save you time attempt to repair the unit yourself to and money before consulting an authorised prevent electric shock or ﬁ re. Have the unit service centre.
www.electroluxaircomfort.com 11 Problem Solution If the defrost mode is started or stopped, you will hear the sound of refrigerant cooling in the reverse direction. The indoor unit cannot blow air. In HEAT mode, when the temperature of the indoor heat exchanger is low, the airﬂ...
12 www.electroluxaircomfort.com indoor unit and outdoor unit will stop • In HEAT mode, the temperature reaches the operation. set value and the compressor has stopped • During defrosting, the indoor indicator operation for 1 minute. ﬂ ashes and the outdoor unit may emit vapour.
www.electroluxaircomfort.com 13 circuit because the circuit operating children. temperature is high. • Install the outdoor unit where there is • The pipes connecting the indoor and sufﬁ cient ventilation. outdoor unit are not included in the unit. • Install the outdoor unit where produced •...
14 www.electroluxaircomfort.com NOTE • Make sure that the live wire, the neutral wire Improper grounding can cause electric and the ground wire in the mains socket are shock. properly connected. • The ground resistance must comply with • Inadequate or incorrect electrical local regulations.
www.electroluxaircomfort.com 15 Indoor unit CAUTION • Check the wiring to make sure that there is no short circuit. Incorrect wiring can cause Installing the mounting plate malfunction. 1. Install the mounting plate horizontally. 1. Open the front panel. 2. Fix the mounting plate to the wall with 2.
16 www.electroluxaircomfort.com CAUTION Hex nut diameter (mm) Tightening torque (Nm) • Check the wiring to make sure that there is Ø 6 15-20 no short circuit. Incorrect wiring can cause Ø 9.52 30-40 malfunction. Ø 12 45-55 1. Remove the handle (x2) on the right side Ø...
www.electroluxaircomfort.com 17 pump changes and compound meter indi- cates 0 instead of minus). 8. Tighten the ﬂ are nut. 9. Make evacuation for 15 minutes or more and check that the compound meter indicates -7.6 x 105 μmHg (-1x105 Pa) (-0,7Bar). 10.
18 www.electroluxaircomfort.com Check after installation Items to be checked Possible malfunction Has the unit been afﬁ xed ﬁ rmly? The unit may drop, shake or emit noise. Have you done the refrigerant leakage test? Insufﬁ cient cooling or heating. Is the thermal insulation sufﬁ cient? Condensation.
www.electroluxaircomfort.com 19 HEALTH FILTER Installation 1. Open the front panel. 2. Remove the air ﬁ lter (A). 3. Attach the health ﬁ lter (B) to the air ﬁ lter (A). 4. Install the air ﬁ lter (A). 5. Close the front panel. Cleaning and maintenance 1.