Preparations Before Installation
Relation of ceiling opening to unit and suspension bolt
Installation Hook Pitch dimensions
Indoor Unit dimensions
Decoration Panel dimensions
Installation Hook (X4)
Ceiling opening dimensions
Adjust positions to ensure the gaps between the Indoor
unit and the four sides of false ceiling are even. The indoor
unit's lower part should sink into the false ceiling for
24mm I 0.9in.
Installation is possible with a ceiling dimension of 600 mm
/ 23.6in (marked with *). However, to achieve a
ceiling-panel overlapping dimension of 15 mm/ 0.6in, the
spacing between the ceiling and the unit should be 20 mm
I 0.8in or less. If the spacing between ceiling and the unit
20 mm I 0.8in, attach sealing mate
recover the ceiling.
S ' S
ial in the part or
Make the ceiling opening needed for installation where
applicable. (For existing ceilings. )
- Create the ceiling opening required for installation. From the
side of the opening to the casing outlet, implement the
refrigerant and drain piping and wiring for remote controller
(unnecessary for wireless type). Refer to each piping or wiring
- After making an opening in the ce由ng, it may be necessary to
reinforce ceiling beams to keep the ceiling level, and to
prevent it from vibrating. Consult the builder for details.
Install the installation hooks. (Use either a MS or M10
size bolt. )
Use expansible hooks, sunken anchors, or other field supplied
parts to reinforce the ce仆ing in order to bear the weight of the
unit. Adjust clearance from the ceiling before proceeding further.
Installation example: see figure below.
Expansible hook (optional)
Installation hook (optional)
For other non-standard installations, contact
your dealer for details.