ELECTRIC DRYER ELECTRICAL REQUIREMENTS
(CANADA ONLY) (LE CANADA SEULEMENT)
Electrical Shock Hazard
Plug into a grounded 4 prong outlet.
Failure to do so can result in death or electrical shock.
It is your responsibility:
To contact a qualified electrical
To be sure that the electrical connection
and in conformance
with the Canadian Electrical Code,
C22.1 - latest edition and all local codes. A copy of the
above codes standard may be obtained from: Canadian
178 Rexdale Blvd., Toronto, ON M9W
To supply the required 4 wire, single phase, 120/240 volt,
60 Hz., AC only electrical supply on a separate 30-amp
circuit, fused on both sides of the line. A time-delay fuse
or circuit breaker is recommended.
Connect to an individual
This dryer is equipped
a CSA International
to be plugged
into a standard
14-30R wall receptacle.
cord is 5 ft (1.52 m) in length.
Be sure wall
reach of dryer's
Do not use an extension
If you are using a replacement
cord, it is recommended
that you use Power
Supply Cord Replacement
Part Number 9831317. For
please reference the service numbers
located in the "Assistance or Service" section.
m For a grounded, cord-connected
This dryer must be grounded. In the event of malfunction or
breakdown, grounding will reduce the risk of electric shock
by providing a path of least resistance for electric current.
This dryer is equipped with a cord having an equipment-
grounding conductor and a grounding
plug. The plug must
be plugged into an appropriate
outlet that is properly
installed and grounded in accordance with all local codes
Improper connection of the equipment-
grounding conductor can result in a risk of electric shock.
Check with a qualified electrician or service representative
or personnel if you are in doubt as to whether the dryer is
properly grounded. Do not modify the plug provided with
the dryer: if it will not fit the outlet, have a proper outlet
installed by a qualified electrician.