PRO-2200 Enclosure PRO22ENC1 & PRO22ENC2 Installation Guide Warnings and Cautions WARNING Before installation, TURN OFF the external circuit breaker which supplies power to the system. Before connecting the device to the power supply, verify that the output voltage is within specifications of the power supply.
PRO-2200 Enclosure PRO22ENC1 & PRO22ENC2 Installation Guide CAUTION If any damage to the shipment is noticed, a claim must be filed with the responsible commercial carrier. CAUTION Electro-static discharge can damage CMOS integrated circuits and modules. To prevent damage always follow these procedures: Use static shield packaging and containers to transport all electronic components, including completed reader assemblies.
PRO-2200 Enclosure PRO22ENC1 & PRO22ENC2 Installation Guide Disclaimer Product Liability; Mutual Indemnification In the event that a Customer receives a claim that a Product or any component thereof has caused personal injury or damage to property of others, Customer shall immediately notify Engineered Systems in writing of all such claims.
PRO-2200 Enclosure PRO22ENC1 & PRO22ENC2 Installation Guide Shipping Instructions To ship equipment back to Engineered Systems: 1. Contact the customer service department before returning equipment at 800-323-4576. Please have the following available when calling: • A description of the problem or reason for returning the equipment.
PRO-2200 Enclosure PRO22ENC1 & PRO22ENC2 Installation Guide Confidentiality All software, drawings, diagrams, specifications, catalogs, literature, manuals and other materials furnished by Engineered Systems relating to the design, use and service of Products shall remain confidential and shall constitute proprietary rights of Engineered Systems, and Customer agrees to treat such information as confidential.
Description The PRO-2200 system is designed for maximum efficient use of wall space through the use of a secure metal cabinet (PRO22ENC1/PRO22ENC2) that can hold up to nine modules, a 4 amp power supply (PRO22E1PS) and a self-contained replaceable backup battery.
PRO-2200 Enclosure PRO22ENC1 & PRO22ENC2 Installation Guide 7. The remainder of the panels can be manually wired for power and RS-485 communications using 18 AWG wire. The wires will be daisy-chained from one panel to the next so the power and the communications are wired in parallel. PRO22DCC is available as an option to be purchased with the equipment.
PRO-2200 Enclosure PRO22ENC1 & PRO22ENC2 Installation Guide 4. Watchman tour 5. Fire alarm supervision (N/A) WIN PAK PRO is not certified for fire alarm supervision 6. Burglar alarm supervision 7. Industrial supervision 8. Other supervisory services NOTE: 2 and 3 may have equal priority: 5 and 6 may have equal priority &...
PRO-2200 Enclosure PRO22ENC1 & PRO22ENC2 Installation Guide 7. Use the Query Analyzer to connect to the WIN-PAK PRO database using the provided script for attachment. 8. Open up the ODBC application in the Control Panel and create a link to the WIN-PAK PRO SQL database.
PRO-2200 Enclosure PRO22ENC1 & PRO22ENC2 Installation Guide 6. Click Next. Change the Server to match the name of the LOCAL PC. The database should be selected as WIN-PAK PRO from that Server. (The destination database). 7. Click Next. Select Transfer objects and data between SQL Server 7.0 database.
PRO-2200 Enclosure PRO22ENC1 & PRO22ENC2 Installation Guide Redundant Test Examples NOTE: Stop watch needed for all three test examples. Example #1 1. Use the MAIN PC’s OFF button to shut it down. Turn on the REDUNDANT PC and start the stop watch.
Relief (non-power limited) Wire Strap Green Lead (from Enclosure to Door) To Battery Enclosure with 40AH Battery Installation Diagram AL400ULX Assembly diagram for use with the PRO22ENC1 and PRO22ENC2 for UL1076 Dimensions 1.3" .875" 1.22" 1.22" (2.22cm) (3.3cm) (3.1cm) (3.09cm)
10. Wire the tamper switch, AC Fail and Battery Fail to assigned inputs. 11. Wire the PRO22ENC1 or PRO22ENC2 tamper switch to the tamper input located on the first panel on the right. 12. The remainder of the panels can be manually wired for power and RS-485 communica- tions using 18 AWG wire.