If, for some reason, Internet connectivity is not available, (for example, your customer's ISP is off line or disconnected), the communicator will transmit signals via the cellular network. These transmissions are sent to the Honeywell NOC and then forwarded to your Central Station exactly the same way as if they were received via the Internet.
The communicator uses 256 bit AES (Rijndael) encryption (which is required for certain government installations). The AlarmNet-i AES Encryption Software Module Version 1.0 contained in the Honeywell products has NIST approval. Listings for this approval can be found at https://csrc.nist.gov/projects/cryptographic-algorithm-validation-program/validation/validation- list/aes and search for “Certification number 979.”...
Section 1: General Information Specifications Mechanical: Dimensions: 15.0"H x 12.75" W x 3.0" D Weight: 10 lbs. 12VDC supplied by the Control Panel. Input Power: Current Drain: 90mA (rms) standby, 105mA (rms) active Network Standard: IEEE 802.3u compliant Ethernet: Data Rate: 10Base-T / 100Base-T with auto detect Ethernet Cable: Cat.
LTE-CF Installation and Setup Guide Compatibility UL – Compatible Control Panels VISTA-32FB FA1670C (First Alert) VISTA-32FBT FA1670CT (First Alert) VISTA-128FBP FA1700C (First Alert) VISTA-128FBPT FA1700CT (First Alert) VISTA-250FBP VISTA-250BPT UL – Compatible Receivers 7810iR-ENT Must be the primary alarm receiver. 8810iR Must be the primary alarm receiver.
S E C T I O N Mounting and Wiring Determine the Signal Quality and Select a Location The communicator must be mounted indoors within the protected premises.
LTE-CF Installation and Setup Guide Mount the Communicator This communicator comes fully assembled with all the components mounted except the external Antenna, and Antenna Mounting Adapter. Refer to the Wiring Diagram on the inside of the back cover for wiring and component identification.
A UL listed control panel must monitor the radio fault output of the communicator. Most Honeywell control panels support ECP data communication. Check the Installation and Setup Guide for the control panel you are using to see if it supports ECP communication.
LTE-CF Installation and Setup Guide Wire the Internet Connection For UL installations, the Ethernet connection between the communicator and the router can- not exceed 20 feet with both the communicator and the router located within the same room. All equipment used for the IP connection (such as the router, hub, modem, etc.) shall be listed, must be powered from an un-switched branch circuit, and be provided with appropriate standby power.
S E C T I O N Programming the Communicator General Information The communicator is designed to deliver alarms via the Internet to an AlarmNet central station or via the cellular network when the Internet is not available.
LTE-CF Installation and Setup Guide Programming for UL864 Compliance This communicator provides a programmable supervision feature that allows the system to meet the UL864 Commercial Fire requirements. These requirements are in the following table. NOTICE TO USERS, INSTALLERS, AUTHORITIES HAVING JURISDICTION AND OTHER INVOLVED PARTIES This product incorporates field programmable software.
Section 3: Programming the Communicator Using a 7720P Programming Tool Connect the 7720P Programming Tool as shown below. The communicator powers the 7720P Programming Tool via the programming jack, and automatically senses the presence of the 7720P when it is plugged in. 7720P PROGRAM CONNECTOR...
LTE-CF Installation and Setup Guide Programming Conventions Programming is accomplished by answering a series of prompts. Most prompts require only a [Y]es or [N]o response, while others require a numerical response (ID numbers, etc.). The current value is displayed on the second line in parentheses ( ). A "?" indicates an invalid entry.
Section 3: Programming the Communicator PROMPTS OPTIONS DESCRIPTION [Y], [N] Exits program mode. Exit Prog. Mode? (Y/N)_ Press [N] to go back to Prompt 3. [ESC] Press [ESC] to load factory defaults. Refer to the Exiting Programming Mode paragraph in this section. 2010 IP &...
LTE-CF Installation and Setup Guide PROMPTS OPTIONS DESCRIPTION This prompt appears only if comm. path includes IP&Cell or Cell. Cell Flt Time [00-60] (60 mins) Enter the time delay (1 – 60) in minutes before the communicator notifies the control panel that there is a communication path failure to AlarmNet over the hard-wired Ethernet connection.
Section 3: Programming the Communicator Exiting Programming Mode To exit the programming mode, press [N] in response to the "REVIEW?" prompt. Then press [Y] to the "Exit Prog Mode?" prompt. Upon exiting, the root file is updated to log the changes made. A message is displayed telling the user that this step is being executed.
S E C T I O N Registration Registering the Communicator Once you have programmed the communicator, it must be registered to enable the AlarmNet account.
LTE-CF Installation and Setup Guide Register using the TEST / REGISTRATION Switch Initiate the registration sequence by clicking the TEST / REGISTRATION switch three times. You can monitor the registration process by viewing the Status Display. The Message (yellow) LED and the Status (green) LED will blink slowly in unison while registration is in progress. Once the registration has been completed successfully, the communicator enters normal operating mode;...
Section 4: Registration Replacing an existing communicator This prompt appears after pressing the [Shift] and down arrow  on Enter PIN# the 7720P. NOTE: If it is necessary to exit registration mode, press ESC from the 7720P programming tool. Enter a 4-digit alphanumeric PIN number provided by your central station, your dealer or an authorized AlarmNet representative.
LTE-CF Installation and Setup Guide IP Information Display NIC IP Address Displays the IP address assigned to this device. xxx.xxx.xxx.xxx Press the [Space] key to go to the next field. NOTE: The Subnet Mask, Gateway IP Addr, DSN Serv IP and DHCP are only displayed if the Comm Path Choice is “IP&Cell”...
Section 5: Programmer Keyboard Commands LTE Displays Signal Display for LTE RAT RSRP RSRQ RAT – Radio Access Technology. xxxx xxxx RSRP – Reference Signal Received Power RSRQ – Reference Signal Received Quality Press the [space] key to get to the next screen. Press the [backspace] key to go to the previous field.
LTE-CF Installation and Setup Guide Operating with 3G Service Signal Display for 3G RAT RSCP EC/No RAT – Radio Access Technology. -xxx -xxxxxx RSCP –Received Signal Code Power Ec/N0 – Carrier Noise Ratio (CNR) Press the [space] key to get to the next screen. Press the [backspace] key to go to the previous field.
Section 5: Programmer Keyboard Commands System Status Display ECP Mode Displays the system status. Flt – Represents radio faults: OK = Normal ; No fault I – No network connectivity over IP and fault time has expired i – No network connectivity over IP and fault time has NOT yet expired.
S E C T I O N Network Diagnostics Running Network Diagnostics The network diagnostic process tests the integrity of the links between the communicator and the various connection points of AlarmNet Control that are known as "REDIRECTORS"...
LTE-CF Installation and Setup Guide Possible Errors Running Network Diagnostics Errors may occur either while tracing the connection to a given Redir or while testing the service at a given Redir. The following list highlights the most common errors. Please contact the AlarmNet Technical Assistance Center (TAC) for help regarding any errors NOT listed below: Possible Errors While tracing the connection to Redir x, the trace fails before ever...
(e.g., www.yahoo.com) into numerical IP addresses (e.g., 188.8.131.52.). Digital Subscriber Line. Enhanced Console Protocol, which is a proprietary bus used in Honeywell control panels to communicate with keypads and peripheral devices. It uses four wires; power, ground, data in, data out.
Wiring Diagram ANTENNAS NUT, WASHER ANTENNA MOUNTING ADAPTER CABINET DOOR FACTORY USE ONLY STATUS SIGNAL CELLULAR QUALITY / MESSAGE 7720P STATUS LED MODE PROG. PORT FAULT STATUS LEDs TB 1 TEST/ REGISTRATION MODE SWITCH SWITCH To Facility Ground NETWORK TB 1 CONNECTIVITY LEDs NOT USED...
(2) This device must accept any interference received, including interference that may cause undesired operation. Responsible Party / Issuer of Supplier’s Declaration of Conformity: Honeywell International, 2 Corporate Center Drive., Melville, NY 11747, Ph: 516-577-2000 RF Exposure Warning –...