INSTALLATION MANUAL FOR OUTDOOR UNIT
Selection of installation site
It should be installed at places where it is firm enough to withstand the weight of the air conditioner to
Typhoon and earthquake prevention. It should be installed according to specific requirements.
Inasppropriate installation may lead to accidents.
(1)During installation, connect the outdoor unit and align
the mounting surface(See the figure on the right).Mount
the electric distribution device on the external side of
the unit in accordance to the installation instructions for
electric distribution device.
(2)To ensure good performance of the machine and facili-
tate installation and maintenance, adequate space must
be reserved (See figure on the right).
Note: Obstacles should be 2000mm off the top of the out-
door unit. Obstacles nearby should be 400mm lower
than the top of the unit.
As there is no protective package for the outdoor unit,so
the following points merit attention:
(1) When forklift is used, insert the fork into the holes in
the base plate.
(2) When crane is used, lift the unit with 4 pieces of steel
rope with diameter above 6 mm.
(3) Put protective materials between the cable and the
unit to prevent deformation and damage of the surface.
(1) The distance between two connections
must not beless than 20mm.
A vertical view of the outdoor unit
Mounting and maintenance
M12 foundation bolt
(4 pieces each)