INSTALLATION MANUAL FOR INDOOR UNIT
All Wiring of this installation must comply with NATIONAL, STATE AND LOCAL REGULATIONS. These
instructions do not cover all variations for every kind of installation circumstance. Should further information be
desired or should particular problems occur, the matter should be referred to your local distributor.
BE SURE TO READ THESE INSTRUCTIONS CAREFULLY BEFORE BEGINNING INSTALLATION. FAI-
LURE TO FOLLOW THESE INSTRUCTIONS COULD CAUSE SERIOUS INJURY OR DEATH, EQUIPMENT
MALFUNCTION AND/OR PROPERTY DAMAGE.
1. Before installation [Before finishing installation, do not throw the attached parts installation
Confirm the way to move the unit to the installation place.
Before moving the unit to the installation place, do not remove their packages.
When have to remove the package, use a soft material or protection board with rope to lift the unit
assembly to avoid unit damage or bumping a scrape.
2. Choose installation place
(1) The chosen installation place should meet the following requirements and get the userís consent.
Place ensures ideal airflow distribution.
The passage of airflow has no obstacles.
When importing outside air, it should be imported directly from outdoors. (if the pipe can not be
extended, it also can not be imported from top)
Place ensures enough space for maintenance.
The pipe length between indoor and outdoor unit is in the permitted limit (referring to outdoor unit
The indoor unit, outdoor unit, electric wire and connection wire is at least 1m away from television
and radio. This is to avoid the image disturbance and noise caused by the above-mentioned home
appliance. (Even if 1m away, if the electromagnetic wave is too strong, it can also cause noise.)
(2) The height of ceiling
The indoor unit can install on the ceiling, which height is no more than 3m.
(3) Install and use the hoisting screw. Check if the installation place can bear the weight of unit
If not certain, strengthen it before install the unit.