Owner’s Manual GENERATOR EB10000 Click to Save As o2016 Honda Motor Co., Ltd. -All Rights Reserved...
The information and specifications included in this publication were in effect at the time of approval for printing. Honda Motor Co., Ltd. reserves the right, however, to discontinue or change specifications or design at any time without notice and without incurring any obligation whatsoever.
When your generator needs scheduled maintenance, keep in mind that your Honda servicing dealer is specially trained in servicing Honda generators and is supported by the parts and service divisions of American Honda. Your Honda servicing dealer is dedicated to your satisfaction and will be pleased to answer your questions and concerns.
A FEW WORDS ABOUT SAFETY Your safety and the safety of others are very important. And using this generator safely is an important responsibility. To help you make informed decisions about safety, we have provided operating procedures and other information on labels and in this manual.
CONTENTS GENERATOR SAFETY ................6 IMPORTANT SAFETY INFORMATION ..........6 Operator Responsibility..............6 Carbon Monoxide Hazards..............6 Electric Shock Hazards ..............7 Fire and Burn Hazards ...............7 Refuel With Care ................8 SAFETY LABEL LOCATIONS..............9 CONTROLS & FEATURES...............10 COMPONENT & CONTROL LOCATIONS...........10 CONTROLS...................12 Fuel Valve Lever................12 Engine Switch ..................12 Choke Knob ..................12 AC Circuit Protectors ...............13...
CONTENTS OPERATION .....................28 SAFE OPERATING PRECAUTIONS.............28 STARTING THE ENGINE ..............29 STOPPING THE ENGINE ..............32 GFCI OPERATION CHECK ..............33 GFCI System ① (120V-30A, 120V/240V-30A, 120V/240V-37.5A Receptacles)..34 GFCI System ② (120V-20A Duplex Receptacle) ......36 AC OPERATION..................38 AC Applications................39 AUTO THROTTLE SYSTEM..............40 STANDBY POWER ................41 Connections to a Building’s Electrical System ......41 System Ground ................41 Special Requirements..............42...
Emission Control System Information...........77 Air Index ...................79 Specifications ...................80 Wiring Diagram................81 CONSUMER INFORMATION ..............82 Dealer Locator Information .............82 Honda Publications................82 Customer Service Information............83 Distributor’s Limited Warranty ............84 Emission Control System Warranty ..........89 ASSEMBLY ....................94 SAFETY....................94 The Importance of Proper Assembly ..........94 Important Safety Precautions ............95...
GENERATOR SAFETY IMPORTANT SAFETY INFORMATION Honda generators are designed for use with electrical equipment that has suitable power requirements. Other uses can result in injury to the operator or damage to the generator and other property. Most injuries or property damage can be prevented if you follow all of the instructions in this manual and on the generator.
GENERATOR SAFETY Electric Shock Hazards • The generator produces enough electric power to cause a serious shock or electrocution if misused. • Using a generator or electrical appliance in wet conditions, such as rain or snow, or near a pool or sprinkler system, or when your hands are wet, could result in electrocution.
GENERATOR SAFETY Refuel With Care Gasoline is extremely flammable, and gasoline vapor can explode. Do not refuel during operation. Allow the engine to cool if it has been in operation. Refuel only outdoors in a well-ventilated area and on a level surface. Never smoke near gasoline, and keep other flames and sparks away.
GENERATOR SAFETY SAFETY LABEL LOCATIONS These labels warn you of potential hazards that can cause serious injury. Read them carefully. If a label comes off or becomes hard to read, contact your Honda servicing dealer for a replacement.
CONTROLS & FEATURES COMPONENT & CONTROL LOCATIONS Use the two illustrations on these pages to locate and identify the most frequently used controls. ENGINE SWITCH GFCI RESET BUTTON CHOKE KNOB AC CIRCUIT GFCI TEST BUTTON BREAKER AC CIRCUIT PROTECTORS i-MONITOR AUTO THROTTLE SWITCH...
CONTROLS & FEATURES FUSE FUEL TANK CAP FUEL GAUGE OIL LEVEL DIPSTICK AIR CLEANER OIL FILLER CAP MAINTENANCE COVER MUFFLER FUEL VALVE LEVER SPARK PLUG CAP BATTERY SPARK PLUG CAP OIL FILTER OIL DRAIN BOLT...
CONTROLS & FEATURES CONTROLS Fuel Valve Lever The fuel valve lever is located between the fuel tank and carburetor. The fuel valve lever must be in the ON position for the engine to run. After stopping the engine, turn the fuel valve lever to the OFF position.
CONTROLS & FEATURES AC Circuit Protectors The AC circuit protectors will automatically switch to OFF if there is a short circuit or a significant overload of the generator at each receptacle. If an AC circuit protector switches OFF automatically, check that the appliance is working properly and does not exceed the rated load capacity of the circuit before resetting the AC circuit protector ON.
CONTROLS & FEATURES AC Circuit Breaker The AC circuit breaker will automatically switch OFF in the following cases. • If there is a short circuit or a significant overload at the receptacles. • If there is a ground-fault current from either receptacles A, B or C. The AC circuit breaker may be used to switch the generator power ON or OFF .
CONTROLS & FEATURES Ground Fault Circuit Interrupter (GFCI) This generator has two types of Ground Fault Circuit Interrupter (GFCI) systems, GFCI system ① and GFCI system ② . GFCI System ① (120V-30A, 120V/240V-30A, 120V/240V-37.5A RECEPTACLES) If there is a ground-fault current from either A, B or C receptacle, it will shut off the power to receptacles A, B, and C.
CONTROLS & FEATURES All receptacles on the generator are protected by a Ground Fault Circuit Interrupter (GFCI) for protection against the shock hazard of ground-fault current. An example of ground-fault current is the current that would flow through a person who is using an appliance with faulty insulation and, at the same time, is in contact with an electrical ground such as a plumbing fixture, wet floor, or earth.
CONTROLS & FEATURES ® Auto Throttle System ® The Auto Throttle system automatically reduces engine speed when all loads are turned off or disconnected. When appliances are turned on or reconnected, the engine returns to the rated speed. Switch Position ON: Recommended to minimize fuel consumption and further reduce noise levels when no load is applied to the generator.
CONTROLS & FEATURES Folding Handle The foldable handle is intended for ease of transportation and should be folded when the generator is stationary. Do not rest objects on the extended handle. To Extend The Handle Lift handle upward. Lock levers will lock and secure the handle into place.
CONTROLS & FEATURES FEATURES ® Oil Alert System ® The Oil Alert system is designed to prevent engine damage caused by an insufficient amount of oil in the crankcase. Before the oil level in the crankcase can fall below a safe limit, the Oil Alert indicator will come on and the Oil Alert system automatically will stop the engine (the engine switch will remain in the ON position).
CONTROLS & FEATURES i-Monitor The i-Monitor is a user interface that allows the operator to view (when the generator is running) total operating time in hours, generator output voltage, battery voltage, and error messages. i-Monitor at Start Up When the engine switch is turned to the ON position, all segments of the i-Monitor display turn on for a second.
CONTROLS & FEATURES i-Monitor Display The four-digit screen displays the total operating hours, battery voltage, and power output voltage or any activated error messages. FOUR-DIGIT SCREEN DISPLAY Total Operating Hours This mode displays the total operating hours of the generator. When the generator is running, the total operating time accumulates.
CONTROLS & FEATURES Power Output Voltage This mode displays an approximate single-phase output voltage. Battery Voltage This mode displays the battery condition, expressed in Volts DC. The battery voltage can be displayed from 8 V up to 16 V. When the battery voltage is less than 8 V, the i-Monitor shows 8 V. When above 16 V, 16 V is shown.
If the generator has a system malfunction, it will show an error message on the i-Monitor display. If an error message displays, contact an authorized Honda generator dealer. When there are a number of errors, they are indicated alternately for two seconds for each.
CONTROLS & FEATURES Ground Terminal The ground terminal is connected to the frame of the generator, the metal non-current-carrying parts of the generator, and the ground terminals of each receptacle. Before using the ground terminal, consult a qualified electrician, electrical inspector, or local agency having jurisdiction for local codes or ordinances that apply to the intended use of the generator.
CONTROLS & FEATURES Fuel Gauge The fuel gauge is a mechanical device that measures the fuel level in the tank. The red indicator in the window will reference the level in relation to full or empty. To provide increased operating time, start with a full tank before beginning operation.
BEFORE OPERATION ARE YOU READY TO GET STARTED? Your safety is your responsibility. A little time spent in preparation will significantly reduce your risk of injury. Knowledge Read and understand this manual. Know what the controls do and how to operate them. Familiarize yourself with the generator and its operation before you begin using it.
BEFORE OPERATION Check the Engine • Before each use, look around and underneath the engine for signs of oil or gasoline leaks. • Check the oil level (see page 48). A low oil level will cause the Oil Alert system to shut down the engine. •...
OPERATION SAFE OPERATING PRECAUTIONS Before operating the generator for the first time, review chapters GENERATOR SAFETY (see page 6) and BEFORE OPERATION (see page 26). For your safety, do not operate the generator in an enclosed area such as a garage. Your generator’s exhaust contains poisonous carbon monoxide gas that can collect rapidly in an enclosed area and cause illness or death.
OPERATION STARTING THE ENGINE SAFE OPERATING PRECAUTIONS Refer to on page 28. 1. Make sure that all appliances AC CIRCUIT BREAKER are disconnected from the AC receptacle. 2. Make sure that the AC circuit breaker is in the OFF position. 3.
OPERATION 5. Make sure the Auto Throttle AUTO THROTTLE SWITCH switch is in the OFF position, or more time will be required for warm up. 6. Start the engine. Turn the engine switch to the START START position, and hold it there until the engine starts.
OPERATION 7. If the choke knob was pulled to the CLOSED position to start the engine, gradually move it to OPEN the OPEN position as the engine warms up. CHOKE KNOB 8. If you wish to use the Auto AUTO THROTTLE SWITCH Throttle system, turn the Auto Throttle switch to the ON position after the engine has...
OPERATION STOPPING THE ENGINE To stop the engine in an emergency, simply turn the engine switch to the OFF position. Under normal conditions, use the following procedure. 1. Turn off or disconnect all AC CIRCUIT BREAKER appliances that are connected to the generator.
Always perform the GFCI system inspection before using the generator. If the GFCI system fails the test, the generator must be repaired by an authorized Honda servicing dealer before use. GFCI SYSTEM ① (120V-30A, 120V/240V-30A, 120V/240 V-37.5 A RECEPTACLES) GFCI SYSTEM ②...
• The RESET button should pop out, and the AC circuit breaker should switch to the OFF position. • If the GFCI and AC circuit breaker do not function as described, take the generator to an authorized Honda generator dealer for repair. TEST BUTTON RESET BUTTON...
ON position. The AC circuit breaker will not remain in the ON position if the RESET button is extended. • If the GFCI and AC circuit breaker do not function as described, take the generator to an authorized Honda generator dealer for repair. RESET BUTTON...
• If the green indicator does not light on, press the RESET button. • If the red indicator starts to blink continuously, contact an authorized Honda generator dealer. 5. Press the TEST button: • The RESET button will pop out and the green indicator will go off.
6. Press the RESET button: • The green indicator will light continuously. • If the red indicator starts to blink continuously, contact an authorized Honda generator dealer. INDICATOR RESET BUTTON When the RESET button pops out or the green indicator does not lit during operation: •...
OPERATION AC OPERATION If an appliance begins to operate abnormally, becomes sluggish, or stops suddenly, turn it off immediately. Disconnect the appliance, and determine whether the problem is in the appliance or the rated load capacity of the generator has been exceeded. Substantial overloading may damage the generator.
OPERATION AC Applications Before connecting an appliance or power cord to the generator: • Make sure that it is in good working order. Faulty appliances or power cords can create a potential for electrical shock. • If an appliance begins to operate abnormally, becomes sluggish, or stops suddenly, turn it off immediately.
OPERATION ® AUTO THROTTLE SYSTEM With the switch in the ON position, engine speed is automatically reduced when ALL loads are turned OFF or disconnected. When appliances are turned ON or reconnected, the engine returns to rated ® speed. In the OFF position, the Auto Throttle system does not operate.
OPERATION STANDBY POWER Connections to a Building’s Electrical System Connections for standby power to a building’s electrical system must be made by a qualified electrician. The connection must isolate the generator power from utility power, and must comply with all applicable laws and electrical codes.
OPERATION Special Requirements There may be Federal or State Occupational Safety and Health Administration (OSHA) regulations, local codes, or ordinances that apply to the intended use of the generator. Please consult a qualified electrician, electrical inspector, or the local agency having jurisdiction. •...
Remember that an authorized Honda servicing dealer knows your generator best and is fully equipped to maintain and repair it. To ensure the best quality and reliability, use only new, Honda Genuine parts or their equivalents for repair and replacement.
SERVICING YOUR GENERATOR MAINTENANCE SAFETY Some of the most important safety precautions follow. However, we cannot warn you of every conceivable hazard that can arise in performing maintenance. Only you can decide whether or not you should perform a given task. Improper maintenance can cause an unsafe condition.
(1) Service more frequently when used in dusty areas. (2) These items should be serviced by your servicing dealer, unless you have the proper tools and are mechanically proficient. Refer to the Honda shop manual for service procedures. See ‘‘Honda Publications’’ on page 82 for ordering information.
SERVICING YOUR GENERATOR REFUELING With the engine stopped, check the fuel level gauge. Refill the fuel tank if the fuel level is low. Gasoline is highly flammable and explosive. You can be burned or seriously injured when handling fuel. • Stop the engine and keep heat, sparks, and flame away when refueling.
SERVICING YOUR GENERATOR FUEL TANK CAP TETHER UPPER LEVEL MARK (RED) EMPTY FULL UPPER LEVEL MARK (RED) FUEL GAUGE After refueling, reinstall the fuel tank cap securely. FUEL RECOMMENDATIONS This engine is certified to operate on regular unleaded gasoline with a pump octane rating of 86 or higher.
SERVICING YOUR GENERATOR ENGINE OIL LEVEL CHECK Check the engine oil level with the engine stopped and in a level position. 1. Open the maintenance cover to access the oil level dipstick. 2. Remove the oil level dipstick and wipe it clean. 3.
SERVICING YOUR GENERATOR ENGINE OIL CHANGE Drain the oil while the engine is warm to assure rapid and complete draining. 1. Place a suitable container below the engine to catch the used oil. 2. Open the maintenance cover to access the oil filler cap. 3.
SERVICING YOUR GENERATOR AIR CLEANER SERVICE 1. Open the maintenance cover to access the air cleaner. MAINTENANCE COVER 2. Pull the air cleaner cover latch to the unlocked position, and remove the cover. Remove the wing nut from the paper filter element. Remove the paper filter element and foam filter element from the air cleaner case.
SERVICING YOUR GENERATOR 4. Clean the filter elements if they are to be reused. Paper filter element: Tap the filter element several times on a hard surface to remove dirt, or blow compressed air [not exceeding 30 psi (207 kPa, 2.1 kgf/cm )] through the filter element from the air cleaner case side.
SERVICING YOUR GENERATOR FOAM AIR FILTER CLEANING A dirty foam air filter will restrict air flow to the carburetor, reducing engine performance. If you operate the generator in very dusty areas, clean the foam air filter more frequently than specified in the Maintenance Schedule.
SERVICING YOUR GENERATOR SEDIMENT CUP CLEANING The sediment cup prevents water that may be in the fuel tank from entering the carburetor. If the engine has not been run for a long time, the sediment cup should be cleaned. Gasoline is highly flammable and explosive.
SERVICING YOUR GENERATOR 3. Unscrew the sediment cup. 4. Clean the sediment cup in non-flammable or high flash point solvent. 5. Install the sediment cup and a new O-ring. 6. Turn the fuel valve to the ON position and check for leaks. FUEL VALVE LEVER O-RING (Replace) SEDIMENT CUP...
SERVICING YOUR GENERATOR SPARK PLUG SERVICE In order to service the spark plug, you will need a spark plug wrench (commercially available). Recommended spark plugs: ZFR5F (NGK) To ensure proper engine operation, the spark plug must be properly gapped and free of deposits. An incorrect spark plug can cause engine damage.
SERVICING YOUR GENERATOR 4. Inspect the spark plugs. Replace them if the electrode is worn or if the insulator is cracked, chipped, or fouled. 5. Measure the spark plug electrode gap with a wire-type feeler gauge. Correct the gap, if necessary, by carefully bending the side electrode. The gap should be: 0.028–0.031 in (0.7–0.8 mm) SIDE ELECTRODE...
SERVICING YOUR GENERATOR SPARK ARRESTER SERVICE The spark arrester must be serviced every 100 hours to keep it functioning as designed. If the engine has been running, the muffler will be very hot. Allow the muffler to cool before servicing the spark arrester. 1.
SERVICING YOUR GENERATOR 2. Remove the 4 mm self-tapping screw, and remove the spark arrester. SPARK ARRESTER 4 mm SELF-TAPPING SCREW 3. Use a brush to remove carbon deposits from the spark arrester screen. Be careful to avoid damaging the screen. The spark arrester must be free of breaks and tears.
SERVICING YOUR GENERATOR BATTERY SERVICE Your generator’s engine charging system charges the battery while the engine is running. However, if the generator is only used periodically, the battery must be charged monthly to maintain the battery service life. The battery contains sulfuric acid (electrolyte), which is highly corrosive and poisonous.
If rapid loss of electrolyte is experienced, or if your battery seems to be weak causing slow operation of the starter motor, see your authorized Honda generator dealer. 1. Locate the battery. Check the electrolyte level with the generator on a level surface.
SERVICING YOUR GENERATOR Battery Removal WARNING: Battery posts, terminals, and related accessories contain lead and lead compounds. Wash hands after handling. 1. Remove the four 6 mm flange COVER bolts, and remove the cover. 6 mm FLANGE BOLT (4) NEGATIVE (–) CABLE 2.
SERVICING YOUR GENERATOR Battery Charging The battery gives off explosive hydrogen gas during normal operation. A spark or flame can cause the battery to explode with enough force to kill or seriously hurt you. Wear protective clothing and a face shield, or have a skilled mechanic perform the battery maintenance.
In the event of fuse failure, locate the cause of failure and repair it before you continue operation. If the fuse continues to fail, discontinue generator use and consult an authorized Honda generator dealer. 1. Turn the engine switch to the OFF position and remove the key before checking or replacing the fuse.
STORAGE STORAGE PREPARATION Proper storage preparation is essential for keeping your generator trouble-free and looking good. The following steps will help to keep rust and corrosion from impairing your generator’s function and appearance, and will make the engine easier to start when you use the generator again.
After removal from storage, drain the stored gasoline into a suitable container, and fill with fresh gasoline before starting. *Use gasoline stabilizers that are formulated to extend storage life. Follow the manufacturer’s instructions for use. Contact your authorized Honda generator dealer for stabilizer recommendations.
STORAGE Draining the Fuel Tank and Carburetor Gasoline is highly flammable and explosive. You can be burned or seriously injured when handling fuel. • Stop the engine and keep heat, sparks, and flame away. • Handle fuel only outdoors. • Wipe up spills immediately. 1.
STORAGE 2. Pull out the carburetor drain tube end under the fan cover of the engine, and place it in a suitable container. 3. Remove the air cleaner cover (see page 51). 4. Loosen the carburetor drain screw. If the drain screw is difficult to loosen, wrap duct tape around the screwdriver stem until the diameter becomes 8 mm as illustrated.
STORAGE Engine Oil Change the engine oil (see page 49). Engine Cylinder 1. Remove the spark plugs (see page 56). 2. Pour a teaspoon (5 cc) of clean engine oil into each cylinder. 3. Turn the engine for a few seconds by turning the engine switch to the START position to distribute the oil in the cylinders.
STORAGE STORAGE PRECAUTIONS If your generator will be stored with gasoline in the fuel tank and carburetor, it is important to reduce the hazard of gasoline vapor ignition. Select a well ventilated storage area away from any appliance that operates with a flame, such as a furnace, water heater, or clothes dryer.
TRANSPORTING Do not lay the generator on its side when moving, storing, or operating it. Oil or fuel may leak and damage the engine or your property. If the generator has been used, allow it cool for at least 15 minutes before loading the generator on the transport vehicle.
(see page 56). Spark plug wet with fuel Dry and reinstall spark plug. (flooded engine). Fuel filter restricted, carburetor Take the generator to an malfunction, ignition malfunction, authorized Honda servicing dealer, valves stuck, etc. or refer to the shop manual.
(see page 67). refueled with bad gasoline. Refuel with fresh gasoline (see page 46). Fuel filter restricted, carburetor Take the generator to an malfunction, ignition malfunction, authorized Honda servicing dealer, valves stuck, etc. or refer to the shop manual.
Check AC load and reset circuit protector (see page 13). Faulty power tool or appliance. Replace or repair power tool or appliance. Stop and restart the engine. Faulty generator. Take the generator to an authorized Honda servicing dealer, or refer to the shop manual.
TECHNICAL INFORMATION Serial Number Location ENGINE SERIAL NUMBER FRAME SERIAL NUMBER Record the engine and frame serial numbers and date purchased in the spaces below. You will need this serial number when ordering parts, and when making technical or warranty inquiries. Engine serial number: Frame serial number: Date purchased:...
High altitude performance can be improved by specific modifications to the carburetor. If you always operate your generator at altitudes above 5,000 feet (1,500 meters), have your authorized Honda servicing dealer perform this carburetor modification. This engine, when operated at high altitude with the carburetor modifications for high altitude use, will meet each emission standard throughout its useful life.
The following instructions and procedures must be followed in order to keep the emissions from your Honda engine within the emission standards. Tampering and Altering Tampering is a violation of Federal and California law.
• Black exhaust smoke or high fuel consumption Replacement Parts The emission control systems on your new Honda engine were designed, built, and certified to conform with EPA and California emission regulations. We recommend the use of Honda Genuine parts whenever you have maintenance done.
TECHNICAL INFORMATION Air Index (Models sold in California) An Air Index Information label is applied to engines certified to an emission durability time period in accordance with the requirements of the California Air Resources Board. The bar graph is intended to provide you, our customer, the ability to compare the emissions performance of available engines.
TECHNICAL INFORMATION Specifications Dimensions Model EB10000 Type AH1 type Description code EBVC Length 41.0 in (1,041 mm) Width 27.7 in (703 mm) Height 35.1 in (891 mm) Dry mass [weight] 400.8 lbs (181.8 kg) Engine Model GX630H Engine type 4-stroke, overhead valve, 2 cylinder Displacement 42.0 cu-in (688 cm...
CONSUMER INFORMATION Dealer Locator Information To find an authorized Honda Servicing Dealer anywhere in the United States: Visit our web site: http://powerequipment.honda.com/dealer-locator Honda Publications Shop Manual This manual covers complete maintenance and overhaul procedures. It is intended to be used by a skilled technician.
CONSUMER INFORMATION Customer Service Information Honda Power Equipment dealership personnel are trained professionals. They should be able to answer any question you may have. If you encounter a problem that your dealer does not solve to your satisfaction, please discuss it with the dealership’s management.
What American Honda will Repair or Replace Under Warranty: American Honda will repair or replace, at its option, any part that is proven to be defective in material or workmanship under normal use during the applicable warranty time period. Warranty repairs and replacements will be made without charge for parts or labor.
CONSUMER INFORMATION To Obtain Warranty Service: You must, at your expense, take the Honda Power Equipment product, accessory, replacement part, apparel, or the power equipment on which the accessory or replacement part is installed, and proof of purchase to any Honda Power Equipment dealer in the United States, Puerto Rico, or the U.S.
Disclaimer of Consequential Damage and Limitation of Implied Warranties: American Honda disclaims any responsibility for loss of time or use of the product, transportation, commercial loss, or any other incidental or consequential damage. Any implied warranties are limited to the duration of this written limited warranty.
What American Honda Will Repair or Replace Under Warranty: American Honda will repair or replace, at its option, any Honda Power Equipment accessories, replacement parts, or apparel that are proven to be defective in material or workmanship under normal use during the applicable warranty time period.
Disclaimer of Consequential Damage and Limitation of Implied Warranties: American Honda disclaims any responsibility for loss of time or use of the product, or the power equipment on which the product is installed, transportation, commercial loss, or any other incidental or consequential damage.
13 provinces and territories of Canada. In the remainder of this Emission Control System Warranty, American Honda Motor Co., Inc. and Honda Canada Inc. will be referred to as Honda. Your Warranty Rights And Obligations...
You are responsible for presenting your power equipment engine to a Honda Power Equipment dealer as soon as a problem exists. The emission related warranty repairs should be completed in a reasonable amount of time, not to exceed 30 days.
Honda power equipment engines sold in the United States and Canada are covered by this warranty for a period of two years from the date of delivery to the original retail purchaser or the length of the Honda Distributor’s Limited Warranty, whichever is longer. This warranty is transferable to each subsequent purchaser for the duration of the warranty period.
You must, at your own expense, take your Honda Power Equipment engine or the product on which it is installed, along with your sales registration card or other proof of original purchase date, to any Honda Power Equipment dealer who is authorized by Honda to sell and service that Honda product during their normal business hours.
Tubing, fittings, seals, gaskets, and clamps associated with these listed systems. Note: This list applies to parts supplied by Honda and does not cover parts supplied by the equipment manufacturer. Please see the original equipment manufacturer’s emissions warranty for non-Honda parts.
ASSEMBLY SAFETY The Importance of Proper Assembly Proper assembly is essential to operator safety and the reliability of the generator. Any error or oversight made by the person assembling and servicing a unit can easily result in faulty operation, damage to the generator, or injury to the operator.
ASSEMBLY Important Safety Precautions • Make sure you have a clear understanding of all basic shop safety practices and that you are wearing appropriate clothing and safety equipment. When performing this assembly, be especially careful of the following: □ Read the instructions before you begin, and be sure you have the tools and skills required to perform the tasks safely.
ASSEMBLY ASSEMBLY Unpacking 1. Remove the generator and loose parts box from the carton. 2. Compare the loose parts with the inventory list below. Tools Required: 12 mm wrench (2), pliers Do not add fuel or oil before tipping the generator. Oil or fuel may damage the engine or your property.
ASSEMBLY Handle Installation Install the handle assembly on the generator upper frame using the 12 mm washers, spring washers and handle holder bolts. TORQUE: 17–22 lbf·ft (24–29 N·m, 2.4–3.0 kgf·m) HANDLE HOLDER BOLT (2) SPRING WASHER (2) 12 mm WASHER (2) HANDLE ASSEMBLY To extend handle: Raise the handle to the horizontal position.
ASSEMBLY Wheel Kit Installation 1. Install the two stands on the under frame using two 8×20 mm flange bolts, two 8×45 mm flange bolts, and two collars. 2. Install the two wheels on the axle shaft using the plain washers and split pins.
ASSEMBLY Hanger Kit Installation 1. Remove the center beam. 2. Loosely install the hanger to the center beam using the hanger bracket and two 8×20 mm flange bolts. 3. Reinstall the center beam. Make sure to tighten the four 8×16 mm bolts securely.
INITIAL USE INSTRUCTIONS Engine Oil The generator is shipped WITHOUT OIL in the engine. 1. Place the generator on a level surface. 2. Open the maintenance cover. 3. Remove the oil filler cap and oil level dipstick. 4. Add enough oil to bring the oil level to the upper limit mark on the oil dipstick.
INITIAL USE INSTRUCTIONS Fuel Add fuel to the generator in a well-ventilated area. Never refuel the engine inside a building where gasoline fumes may reach flames or sparks. Keep gasoline away from appliance pilot lights, barbecues, electric appliances, power tools, etc. Spilled fuel is not only a fire hazard, it causes environmental damage.
Please Register Your Generator If your dealer did not collect registration information from you, please take a few minutes and register your purchase with Honda. This allows us to contact you with any important updates regarding your generator. Please note registration is not required to obtain warranty service.
INDEX AC Applications .................. 39 AC Circuit Breaker................14 AC Circuit Protectors ................13 AC OPERATION................... 38 AIR CLEANER SERVICE ..............51 Air Index ....................79 ARE YOU READY TO GET STARTED?..........26 ASSEMBLY..................94, 96 AUTO THROTTLE SYSTEM............17, 40 Battery Charging.................
INDEX i-Monitor....................20 IMPORTANT SAFETY INFORMATION ..........6 Important Safety Precautions ............95 INDEX ....................103 INITIAL USE INSTRUCTIONS ............100 IS YOUR GENERATOR READY TO GO?..........26 Knowledge ..................26 Loose Parts..................96 MAINTENANCE SAFETY..............44 MAINTENANCE SCHEDULE .............. 45 NO POWER AT THE AC RECEPTACLES..........
INDEX SAFE OPERATING PRECAUTIONS............ 28 SAFETY....................94 SAFETY LABEL LOCATIONS..............9 Safety Precautions................44 SEDIMENT CUP CLEANING............... 54 Serial Number Location ..............75 SERVICING YOUR GENERATOR ............43 SPARK ARRESTER SERVICE.............. 58 SPARK PLUG SERVICE............... 56 Special Requirements ................ 42 Specifications..................