8-1. Using with master system controller
When connecting multiple system controllers, the system controller with many functions is designated
as the "master", and the system controllers with few functions are designated as the "slaves". The
"master/slave" functions of the system controller used together are as follows.
The functions have a priority in order of G50 (MJ-103MTRA) > PAC-SF44SRA > PAC-YT34STA >
PAC-YT40ANRA > PAC-SC30GRA > LMAP02-E (LMAP03U).
8-2. Setting local remote controller operation prohibit function
from this controller
When connecting several system controllers, and setting the "local remote control operation
prohibit" function from this controller, set this controller's "operation prohibit setting changeover"
to "ON (permit)".
(The 9-1 External signal input function cannot be used when this function is set to disable.)
8-3. Prohibiting operation of system controller other than this
To prohibit the operation of a system controller other than this controller when the local remote
control operation is set to prohibit with this controller, set this controller's "operation prohibit range
changeover" to "ON (including system controller)."
Only local remote control
Including system controller
8-4. Changing set temperature display to "Fahrenheit display"
Fahrenheit display :
After changing the switch 3 1,4 to 6 ON/OFF status, always turn the power OFF.
The function will change only after the power is turned OFF and ON.
SW3-1 : OFF
SW3-1 : ON
SW3-4 : OFF
SW3-4 : ON
SW3-5 : OFF
SW3-5 : ON
SW3-6 : OFF
SW3-6 : ON