<List of system remote controller functions>
(*1) Refer to page 33.
(*2) This controller (system remote controller) is one of the system controllers.
(*3) Refer to page 29.
(*4) This controller does not have a clock function.
11-2. Main specifications
Working environment conditions
Interlocked unit setting
Master system controller
/slave system controller (*1)
controller own address
Time setting (*4)
range limit mode
Indoor units, LOSSNAY
Number of indoor units and
Number of local remote
controllers in one group
Number of system controllers
controlling one group (*2)
Number of indoor units
linked with one LOSSNAY
30VDC (supplied from indoor unit or power feed unit for transmission line (type: PAC-SC34KUA).
Temperature 0 to 40
Set the unit (indoor unit, LOSSNAY remote controller, slave system controller)
Set interlocking with the LOSSNAY and indoor unit.
Set the system controller as the master or slave.
Set whether to prohibit operation with the local remote controller using this
controller or with another controller.
Set whether to prohibit operations for the remote control with this
Set the set temperature display to a Celsius or Fahrenheit display.
Set the system remote controller's own address (Refer to the
The current time can be set collectively for system controllers and remote
controls provided with the time setting function.
The set temperature range can be set collectively for remote controls
provided with the set temperature range limit mode function.
Maximum 50 units (Maximum 50 groups)
0 to 16 units (The indoor unit and LOSSNAY cannot be registered
in the same group.)
0 to 2 units
0 to 4 units (Includes the number of local remote controllers for one
group.) 0 to 3 units in group having one local remote controller
0 to 16
C / 32 to 104
F, humidity 30 to 90%RH (with no dew condensation)
16 x 3