4. Save Settings and Device Baseline
1. Perform any needed diagnostic tests and run tests. See the SVI II AP DTM online help for
steps to configure and run diagnostic tests. Save the results.
2. After finishing with the control valve, make sure all saved reports contain all necessary
order information, by:
a. Right-clicking the AP device in the Project pane and select Additional Functions >
Report and the report appears.
b. Clicking the Disconnect icon
Clicking Network > Exit to close the DTM. If you have unsaved data, click the
Download Parameters to Device icon
3. Connect the AP wires to next item on order. Click Find New Devices. Go to step 4 of "2.
Software Install and Configuration" on page 6 and repeat.
© 2016 General Electric Company. All rights reserved.
Figure 10 Example Report
Use the icon bar on the top of the report to export this to a Word
or pdf file, which can be printed or saved.
on the ValVue 3 toolbar.
Masoneilan SVI II AP Bench Quick Start Manual