1. Do not connect system to a high pressure or city water
2. Use equipment only in a pool or spa installation.
3. Trapped air in system can cause explosion. BE SURE all
air is out of system before operating or testing equipment.
Before pressure testing, make the following safety
• Check all clamps, bolts, lids, and system accessories
• Release all air in system before testing.
• Water pressure for test must be less than 25 PSI
• Water Temperature for test must be less than 100
• Limit test to 24 hours. After test, visually check system
to be sure it is ready for operation. Remove trap lid and
retighten hand tight only, see Figure 1.
NOTICE: These parameters apply to Sta-Rite equipment
only. For non-Sta-Rite equipment, consult manufacturer.
NOTICE: Do not start the pump until the strainer basket
cover is on and the tab, or rib, on the discharge port
aligns between the arrows.
Always follow basic safety precautions with this
equipment, including the following.
To reduce the risk of injury, do not per-
mit children to use this product unless they are closely
supervised at all times.
This pump is for use with permanently
installed pools and may also be used with hot tubs and
spas if so marked. Do not use with storable pools. A
permanently installed pool is constructed in or on the
ground or in a building such that it cannot be readily
disassembled for storage. A storable pool is con-
structed so that it may be readily disassembled for stor-
age and reassembled to its original integrity.
SA VE THESE
Figure 1 – Strainer basket cover alignment.
Only qualified, licensed personnel should install pump
Pump may be bolted to level
foundation or mounting bracket.
NOTICE: Port threads are: Internal - 2" NPT for direct connec-
tion to pipe. External - 3-1/4" Buttress. Fits Sta-Rite U11-200P
Union Collar for quick disconnect pipe connection.
See Page 13 for Union Kits.
Pump mount must:
Be located away from corrosive or flammable liquids.
Have enough ventilation to maintain air temperature at less
than the maximum ambient temperature rating (Max. Amb.)
listed on the motor model plate. If this pump is installed in
an enclosure/pump house, the enclosure must have ade-
quate ventilation and air circulation to keep the tempera-
ture in the enclosure at or below the motor's rated ambient
temperature whenever the pump is running.
Be solid - Level - Rigid - Vibration free. (To reduce vibra-
tion and pipe stress, bolt pump to mount.)
to Filter or Pool