# Bosch C 950 Installation Manual page 46

46 | Maintenance and service
10F
1P*
Appliance type - Cd (Condensing)
Appliance type - nC (Non condensing)
2P*
Appliance power - 175 / 199 (kBTU/hr)
3P*
Temperature range - H (100-140°F)
Temperature range - C (100-184°F)
H0
H1
H2
C0
C1
C2
Table 50 * Settings define from factory
7.7.1
Working hours
To see how many hours the appliance has worked, please enter the
▶ Select the sub-mode "H0".
Write the number that shows in the display.
▶ Select the sub-mode "H1".
Write the number that shows in the display.
▶ Select the sub-mode "H2".
Write the number that shows in the display.
After checking the sub-modes H0, H1 and H2, introduce the values in
the table below;
Working hours
Number in H0
Number in H1
______ (X 100) =
Number in H2
______ (X 10 000) =
(H0 + H1 + H2) = Total of hours
Table 51
Example:
Calculation of number of working hours,
Working hours
Number in H0
Number in H1
Number in H2
0 (X 10 000) =
(H0 + H1 + H2) = Total of hours
Table 52
7.7.2
Number of cycles
To see how many cycles the appliance has done, please enter the
▶ Select the sub-mode "C0".
Write the number that shows in the display.
▶ Select the sub-mode "C1".
Write the number that shows in the display.
▶ Select the sub-mode "C2".
Write the number that shows in the display.
6 720 805 440 (2014/11)
10th most recent error
Numbers of hours - mode 0
Numbers of hours - mode 1
Numbers of hours - mode 2
Number of cycles - mode 0
Number of cycles - mode 1
Number of cycles - mode 2
______
_______ +
_______ +
_______
__________
60
60 +
5 (X 100) =
500 +
0
560
After checking the sub-modes C0, C1 and C2, introduce the values in a
table as the example;
Example:
Calculation of number of cycles (1 cycle = 1 ignition),
Number of cycles
Number in C0
Number in C1
6 (X 100) =
Number in C2
1 (X 10 000) =
(C0 + C1 + C2) = Total of cycles
Table 53
40
40 +
600 +
10 000
10 640
Greentherm