Specification of the Cabine The APM30H(Ver B) series cabinets consist of the APM30H The APM30H(Ver.B) series cabinets consist of the APM30H, TMC11H IBBS200T and IBBS200D TMC11H, IBBS200T, and IBBS200D. Cabinet dimensions (excluding the TEC cool hood of the e IBBS200T): 600 mm x 700 mm x 480 mm (W x H x D)
1 Installation Procedure Install the Cabinets Install the Ca abinets on the Install the Cabinets on on the Base Meta l Pole the Wall Earth Grou unding the Cabin nets Install the Opt tional Modules Install the e Cables Seal the Ca able Holes Install the Ba atteries and...
2 Installing the Cabinets Installation the Cabinets on th he Base Cabinet dimensions and clearance re equirements (unit: mm) > 60 Cabinet Cabinet Cabinet > 300 > 300 The values in the figure are not for the concrete plinth. Maximum The recommended distance between the cabinets is >...
2 Installing the Cabinets Installation the Cabinets on th he Base Check the base level. Install the bolt with the spring washer and flat washer. Adjust the base level by adding adjusting pads to the bolts between the base and the concrete plinth. Tighten the bolts.
3. Secure the cabinet onto the base. t th b By attaching the IBBS200D as an example, attaching the APM30H or the TMC11H or the Gaske et with an IBBS200T to the base is the same.
2 Installing the Cabinets Installation the Cabinets on th he Base 4. (Optional) Stacking two cabinets. Remove t the plastic Remove the cover plates (×2) Stack the cabinets, and screws (x x4) from the top from the top of the lower attach the cabinets with of the low wer cabinet.
When the APM30H is installed on a metal pole, greas se must be covered. For details, see Appendix e on page 35. Hold the cabinet when opening the door to prevent th he cabinet from tipping over.
2 Installing the Cabinets Installing the Cabinets on the Wall 2. Install the expansion bolt 1. Marking the anchor points assemblies. Anchor Bolt points (×6) Spring washer Drawing Drawing Fl t Flat washer template Expansion tube ≥ Unit: mm Unit: mm 4.
The upper cabinets are connected to the lowe cabinets with the equipotential cables. The lower cabinets are connected with the equipotential cables. The cabinet below the APM30H is connected to the grounding busbar with PGND cables. Wiring copper About the principles for earth grounding the cabinets About the principles for earth grounding the cabinets, takes the following scenario as example.
4 Installing the Optional Mo odules Installing the SOU in the APM 1. Specification of the SOU. Configured with the following four outlet types, the cabinets support different SOU types of different countries. The SOU is preferably installed in the bottom 1 U space of t he cabinet.
4 Installing the Optional Mo odules Installing the EMUA in the APM M30H 1. Install the EMUA. 2. Install the power cable for the EMUA. PWR1 EMUA LOAD7 3. Install the signal cable for the EMUA. t ll th bl f th EMUA COM OU RS485...
4 Installing the Optional Mo odules Installing the SLPU in the APM M30H 2. Install the internal monitoring 1. Install the SLPU. transfer cable for the SLPU. EXT-ALM0 SLPU Internal monitoring transfer cable connections: 3. Install the external dry contact monitoring and alarm signal cable monitoring and alarm signal cable Mapping relationship between the pins in...
Installing the Power Cables (-4 48 V DC) If the APM30H is configured, skip the section. 2.Power cable for the junction box in the bl f th j i th 1.
5 Installing the Cables Installing the Power Cables (+ +24 V DC) If the APM30H (+24 V DC) is not configured, skip the section. 1. Install the input power cable for the APM3 Remove the protecting cap of the power box of the EPS48100D.
Installing the Power Cables (A AC Power Supply Scenario) 2. APM30H-TMC11H Power cables for the TMC11H Power cable for the junction box NEG(-) RTN(+) 3. APM30H - IBBS200D/IBBS200T APM30H:IBBS=1:2 1. Power cables for the IBBS200D/IBBS200T RTN(+) NEG(-) Power series 120 connector Either the IBBS200D or the IBBS200T is installed.
5 Installing the Cables Installing the Power Cables (A AC Power Supply Scenario) 3. APM30H - IBBS200D/IBBS200T LOAD3 APM30H:IBBS=1:2 2. Power cables for the fan in the IBBS200D Easy power receptacle (pressfit FAN/TEC FAN/TEC type) connector RTN(+) NEG(-) For details on how to...
5 Installing the Cables Installing the Power Cables (A AC Power Supply Scenario) 3. APM30H - IBBS200D/IBBS200T APM30H:IBBS=1:2 LOAD2 LOAD3 4. Power cables for the TEC in the IBBS200T FAN/TEC FAN/TEC RTN(+) NEG(-) If the LOAD2 is already occupied, it is recommended...
5 Installing the Cables Installing the Power Cables (A AC Power Supply Scenario) 3. APM30H - IBBS200D/IBBS200T LOAD3 APM30H:IBBS=1:1 2. Power cables for the fan in the IBBS200D / the TEC in the IBBS200T Easy power receptacle (pressfit type) connector...
Cables Principles for routing the monitoring signal cables When the signal cable is routed between cabine ets, coil the extra length of the cable in the base if the cable is redundant. 1. APM30H+IBBS200D/IBBS200T APM30H+IBBS200D APM30H+IBBS200T COM_485 COM_485 COM_OUT...
5 Installing the Cables Installing the Monitoring Sign al Cables 2. APM30H+2 IBBS200D/IBBS200T APM30H+2 IBBS200D COM_485 COM_OUT COM_IN COM_IN APM30H+2 IBBS200T COM_485 COM_IN COM_IN COM_OUT COM_OUT...
6 Sealing the Cable Holes Sealing the Cable Holes in the e Cabinets The cable module for the IBBS200D, IBBS200T, or APM30H H is the same as that for the TMC11H. When two IBBS200Ds or two IBBS200Ts are installed in sta ck mode, the installation of the cable module in the upper cabinet is not required.
7 Installing the Batteries an nd their Cables Installing the Batteries Before installing the batteries, set the battery MCB labeled B BAT to OFF to disconnect the equipment from the battery. Finish the installati on, set the BAT to ON. During the installation of the batteries, use insulated tools su ch as wrenches and screwdrivers, and do not reversely connect the...
8 Checklist for the Installat tion Checklist for the Cabinet Insta allation The installation position of the cabinet str rictly comply with the engineering design. When the cabinet is mounted on a wall, t he holes of the mounting ears are aligned with the bolt holes.
30°C), and the inner air circulation fan rotates in a high speed. The outer air circulation fan in the APM30H H stops in a normal situation (with the ambient temperature of lower than 35°C), and the inner air circulation fan rotates in a low speed.
9 Checking the Power-On S Status AC Power Supply Scenario -48 V DC Power Supply Scenario Start Start Clear the fault Power on the APM30H Power on the TMC11H Power on the TMC11H Clear the fault Clear the fault Is the Are the LEDs...
10 Appendix Assembling the Power Series 120 Connector power series 120 connector, conta act terminal, heat-shrinkable tube, and cable. 1. Material: 2. Procedure for adding the contact ter rminal Lead the cable through the heat- Strip a part of the jacket off the cable so that shrinkable tube, and then place the the conductor with a length of L1 is exposed.
10 Appendix Assembling the Easy Power Rec ceptacle (Pressfit Type) Connector 1. Material: Easy Power Receptacle (Pressfit Type) C Connector, contact terminal, heat-shrinkable tube, and cable 2. Procedure for adding the contact ter rminal Strip the jacket off the cable according to Use a screwdriver to push the sliding block the scale on the equipment.
10 Appendix Replacing the Fuse 1. Remove the extraction tool. 2. Obtain the fuse from the case. 3. Replace the fuse by using the extraction tool. Fuse Align the bulge on extraction tool with the hole on the fuse Fuse Remove the fuse by using the extraction tool...
10 Appendix Repairing the Damaged Paint 1. Codes of color samples Object Color N Name Huawei Color International Code Color Code Cabinets (including APM30H, RFC, RAL70 YB026 RAL7035 TMC11H, IBBS200D and IBBS200T) Base 3010 lig ght grey YB030 Pontone 422U 2.
Grease Grease When the APM30H is installed on a metal pole or on the wall, grease should also be covered around the four bolts which are used to attach the cabinet and trapezoidal rack.
This is the eleventh commercial release. Compared 12 with 11, 1. Add the diameter specification of the metal pole on w hich the Apm30H and TMC11H are installed in the chapter of “Installing the Cabinets”. 11 (2010-08-25) This is the tenth commercial release.
11 Change History 10 (2010-07-15) This is the ninth commercial release. Compared 10 with 09, 1. Add the scenarios of the cabinets in the chapter of “I nstallation Scenarios”. 2. Add the scenarios of the power cables between the AP PM30H and IBBS200D or IBBS200T in the chapter of “Installing the Power Cables (AC Power Supply Scenar rio)”...
HUAWEI TECHNOLOGIES CO., LTD. Huawei Industrial Base Bantian Longgang Shenzhen 518129 518129 People’s Republic of China www.huawei.com...