Chapter 5. Programming
A Program Used When Mounting a Thermocouple Input Module onto the Remote I/O Station
1) System Configuration
2) Initial Settings
(1) Specifying used channel
(2) Specifying thermocouple type: Type K
3) Program Description
(1) _NET0_LIV : Turns "On" if the local normally communicates with the remote.
_NET0_RST : Turns "On" if communications error or power failure occurs. The user has to turn it
off forcedly when the normal state has been restored.
(2) If the temperature conversion value is negative, %Q0.3.0 will be turned "On" and the value will be
changed into a positive value.
(3) If no error has been occurred during execution of the reading function block, the temperature
conversion value will be output to "%QD0.2.0".
: Channel 0
5 - 9