15" quickpanel* view
& quickpanel control (102 pages)
Summary of Contents for GE NetworX NX-4
UL approved for ANSI/SIA CP-01-2000 ™ NetworX Series NX-4 Control Panel Installation and Startup...
This document shall not be reproduced in whole or in part nor shall its contents be disclosed to any third party without the written approval of GE Security. Please refer to the current GE Security product catalog for detailed warranty information.
NX-4 Control GENERAL DESCRIPTION The NetworX NX-4 represents a new approach to security systems design. Drawing on our experience in the world market as the largest exporter of USA manufactured controls we have developed the most flexible, durable, and user- friendly control ever seen in our industry.
NX-4 Control FEATURE DEFINITIONS Abort If enabled, the NX-4 will wait the programmed number of seconds in location 40 prior to sending an alarm. During this delay time, the "Cancel" LED will flash. To abort the report, type in a code and press the [Cancel] key. The LED will extinguish.
NX-4 Control Built In Siren Driver The NX-4 has a built-in 112db siren driver. When desired, this built-in driver can be easily converted to a 1 amp voltage output through programming. (Loc. 37, page 17) Bypass Toggle This feature will enable the end user to toggle (turn on or off) the bypass of an interior zone with the system armed by pressing the [Bypass] key.
NX-4 Control Exit Error If enabled, the NX-4 will send an "Exit Error Report" if an entry/exit zone is faulted at the instant the exit delay expires. This report will be sent along with the user number that armed the system, if the panel is not disarmed before the entry delay expires.
NX-4 Control Local Programming Lockout This feature will disable programming of all locations or specified locations from the keypad. (Loc. 21, page 16) Log Full Report A report can be sent to the central station when the event log is full. (Loc. 37, page 17) Lost Clock Service Light The NX-4 can be programmed to illuminate the "Service"...
NX-4 Control Swinger Shutdown This feature allows a zone(s) to be automatically bypassed after a specified number of alarms. When a zone is tripped, the alarm ‘counter’ reflects “1” in memory. If a new (first) alarm is detected in a different zone, the counter remains at “1”.
NX-4 Control PROGRAMMING THE LED KEYPADS This section describes how to program the address of each keypad as well as the options that are available. The address of the keypad is important because this is how the panel supervises the keypads. The factory default for the Master code is --- when using a 4-digit code or ----- for a 6-digit code.
NX-4 Control CHANGING USER CODES: 1. Enter [r]--[master code]. The "Ready" LED will flash. 2. Enter the 2 digit user number (always 2 digits such as "03" for user 3). The "Ready" LED will illuminate steady. 3. Enter the new user code designated for that individual. The "Ready" LED will flash indicating that the code was accepted.
NX-4 Control PROGRAMMING THE NX-4 CONTROL ENTERING THE PROGRAM MODE: To enter the Program Mode, press [r]-. At this time, the five function LEDs (Stay, Chime, Exit, Bypass, & Cancel) will begin to flash. Next, enter the "Go To Program Code" (FACTORY DEFAULT IS ---).
NX-4 Control PROGRAMMING EXAMPLE – FIGURE 1 (Numerical Data) Zone 1 LED = 1 Zone 2 LED = 2 Data = 9 Data = 66 Zone 4 LED = 8 Zone 7 LED = 64 To change data in a Pressing [#] will exit a segment, enter the data location without...
NX-4 Control FEATURE SELECTION DATA: Feature selection data will display the current condition (on or off) of eight features associated with the programming location and segment selected. Pressing a button on the touchpad (1 thru 8) that corresponds to the "feature number" within a segment will toggle (on/off) that feature. Pressing any numeric key between  and  for selection of a feature, will make the corresponding LED illuminate (feature ON).
NX-4 Control FORMAT SELECTIONS DATA FORMAT DESCRIPTION Local Communicator is disabled Universal 4+2 Two digit event code 1800hz transmit 2300hz handshake double round parity 40pps 3+1 fast (or 4+1) One digit event code 1900Hz transmit 1400Hz handshake double round parity 20pps Reserved Reserved...
NX-4 Control LOCATION 6 - PROGRAMMING PHONE #2 (20 segments, numerical data) Phone #2 is programmed in location 6. A "14" indicates the end of the phone number. Delays of four seconds can be programmed at any point in the phone number by programming a "13" in the appropriate segment. If tone dialing is desired, program a "15"...
NX-4 Control LOCATION 12 - PROGRAMMING PHONE #3 (20 segments, numerical data) Phone #3 is programmed in location 12. A "14" indicates the end of the phone number. Delays of four seconds can be programmed at any point in the phone number by programming a "13" in the appropriate segment. If tone dialing is desired, program a "15"...
NX-4 Control LOCATION 18 - CUSTOM COMMUNICATOR FORMAT (See locations 2, 8, & 14) Segment 1: 1 = On for 1800hz transmit; Off for 1900hz. 2= On for 2300hz handshake; Off for 1400hz. 3= On for cksum parity; Off for double round parity. 4= On for 2 digit event code;...
NX-4 Control Segment 2: 1 - On enables the LED Extinguish feature. 2 - On enables the Require Code for Bypassing feature. 3 - On enables the Zone Bypassed Sounder Alert feature. 4 - On enables the AC Power/Low Battery Sounder Alert feature. (Default is “on”.) 5 - On enables Bypass toggle.
NX-4 Control Segment 4: 1 - On if Fail To Communicate report enabled. 2 - On if Log Full report enabled. 3 - On if Autotest report enabled. 4 - On if Start/End programming report enabled. 5 - On if End Download report enabled. 6 - On if Sensor Low Battery report enabled.
NX-4 Control LOCATION 41 - CODE REQUIREMENTS (1 segment, feature data) Segment 1: 1 = On enables the 6-digit code option. If 6-digit option is enabled, all arm/disarm codes and the "Go To Program Code" must be 6 digits. If this option is enabled, the default user 1 code is ----- .
NX-4 Control AUXILIARY OUTPUT EVENT SELECTION DATA EVENT DATA EVENT / Burglary Alarm Fire Trouble / Fire Alarm Chime / 24 Hour Alarm / Expander Trouble / Trouble Alarm Dynamic Battery Test Time / Tamper Alarm Open Period Yelping Siren (Burglary) Closed Period Temporal Siren (Fire) Listen-In...
NX-4 Control LOCATION 52 - OPENING TIME (2 segments, numerical data) Location 52 contains the time in 24 hour format the NX-4 enables codes designated as arm only after closing. This time is only valid on those days programmed in location 54. NOTE: Opening time must be earlier than closing time for Auto Arm, Aux.
NX-4 Control COMMUNICATOR CODES FOR SLOW FORMATS ONLY LOCATIONS 56- 83 ARE ONLY USED WHEN REPORTING EVENTS TO A PAGER OR USING A SLOW FORMAT SUCH AS 4+2. WHEN USING CONTACT ID OR SIA, THERE IS NO NEED TO PROGRAM THESE LOCATIONS. LOCATION 56 - ARESTORE@ CODE (1 segment, numerical data) Location 56 contains the event code for any zone "Restore"...
NX-4 Control LOCATION 68 - AAC FAIL / AC FAIL RESTORE@ CODES (4 segments, numerical data) Location 68 contains the tens and ones digits for a 4+2 format that will be sent if "AC Fail Reporting" is enabled. Segment 1 contains the tens digit of the "AC Fail Reporting". Segment 2 contains the ones digit of the "AC Fail Reporting".
NX-4 Control LOCATION 81 - ASTART PROGRAM AND END PROGRAM@ CODES (4 segments, numerical data) Location 81 contains the tens and ones digits for a 4+2 format that will be sent if "Start / End Programming Reporting" is enabled. Segment 1 contains the tens digit of the "Start Program Reporting". Segment 2 contains the ones digit of the "Start Program Reporting".
NX-4 Control LOCATIONS 112 THRU 149 contain the remaining 19 Customized Zone Group information. The even numbered locations reflect the AGroup Alarm Event Code@ and the odd numbered locations designate the Group Characteristics. Locations 112 and 113 correspond to Group 2; Locations 148 and 149 correspond to Group 20. Use the description found in Location 110 for programming the Alarm Event Codes, and use Table 1.1 shown on page 24 to select the Group Characteristics.
NX-4 Control PROGRAMMING WORKSHEETS ? Factory defaults for segments are in bold italics text. Some locations are reserved and have been intentionally omitted. DESCRIPTION DEFAULT PROGRAMMING DATA PHONE #1 14-14-14-14-14-14-14-14-14-14- __ __ __ __ __ __ __ __ __ __ 14-14-14-14-14-14-14-14-14-14 __ __ __ __ __ __ __ __ __ __ PHONE #1, ACCOUNT CODE...
NX-4 Control DESCRIPTION DEFAULT DATA FORMAT OVERRIDE Segment #1 (Circle Numbers To Program) Segment #2 (Circle Numbers To Program) On = 1800hz transmit; Off = 1900hz On = pager format (no handshake required) On = 2300hz handshake; Off = 1400hz. On = 1400/2300 handshake On = cksum parity;...
NX-4 Control DESCRIPTION DEFAULT DATA SIREN AND SYSTEM SUPERVISION Segment #1 (Circle numbers to program) Reserved. Reserved. Siren blast at arming. Siren blast at exit delay expiration. Siren blast at closing kissoff. Siren sounds during a cross zone verification time. Siren sounds for a tamper.
NX-4 Control DESCRIPTION DEFAULT DATA KEYPAD SOUNDER CONTROL Segment #1 (Circle numbers to program) Reserved. Reserved. Keypad sounds upon AC Power Failure. Keypad sounds upon Low Battery Detection. Keypad sounds during Cross Zone Trip Time. Keypad sounds for Tamper Alarm. Reserved.
NX-4 Control DESCRIPTION DEFAULT DATA AUXILIARY OUTPUT #1, EVENT & TIME Segment #1: Program the event number for output #1. 0=Burglary alarm Segment #2: Program the timing for output #1 here . 10 seconds AUXILIARY OUTPUT #2, EVENT & TIME Segment #1: Program the event number for output #2.
NX-4 Control DESCRIPTION DEFAULT DATA AUXILIARY 2 KEYPAD PANIC KEYPAD MULTIPLE CODE ENTRY TAMPER BOX TAMPER / BOX TAMPER RESTORE 0-0-0-0 _ _ _ _ AC FAIL / AC RESTORE 0-0-0-0 _ _ _ _ LOW BATTERY / LOW BATTERY RESTORE 0-0-0-0 _ _ _ _ POWER SHORT / POWER SHORT RESTORE...
NX-4 Control THE DEFAULTS LISTED IN THE ODD NUMBERED LOCATIONS BELOW REPRESENT THE THREE SEGMENTS OF EACH OF THOSE LOCATIONS. USE THE THREE SEGMENT CHARTS FROM LOCATION 111 TO UNDERSTAND THESE DEFAULTS. GROUP 2 ALARM EVENT CODE GROUP 2 CHARACTERISTIC SELECT 2-125-78 GROUP 3 ALARM EVENT CODE GROUP 3 CHARACTERISTIC SELECT...
NX-4 Control APPENDIX 1 REPORTING FIXED CODES IN CONTACT ID AND SIA The table below list the event codes sent for the following reports (if enabled) when using CONTACT ID or SIA formats. REPORT CONTACT ID MANUAL TEST AUTOTEST OPEN (user number) CLOSE (user number) CANCEL (user number) DOWNLOAD COMPLETE...
NX-4 Control APPENDIX 2 REPORTING ZONE CODES IN SIA OR CONTACT ID The NX-4 has the ability to report SIA level 1 transmissions to either or both phone numbers. Each report in SIA consists of an Event Code and a Zone or User ID. The Zone ID will be the zone number that is in alarm. The event code will come from the chart below and be programmed in the configuration group event code.
NX-4 Control APPENDIX 3 EXPANDER NUMBERS FOR REPORTING EXPANDER TROUBLE The tables below list the device numbers that will be reported for trouble conditions. Device Device # reported NX-4 Control Panel See pages 33 - 34 for possible report codes. NX-534E Two Way Listen-In NX-540E AOperator@ NX-582E AES Interface...
NX-4 Control TERMINAL DESCRIPTIONS TERMINAL DESCRIPTION House Telephone Ring (Grey). Telephone Ring (Red). Telephone Tip (Green). House Telephone Tip (Brown). AC input. Connect to a 16.5V 25, 40 or 50 VA Class ll U.L. approved transformer. EARTH Earth Ground. Connect to a cold water pipe or a 6 to 10 foot driven rod. Connect negative lead of low current device [relay, LED (install 1K Ω...
NX-4 Control Notices (Applies to products which have the CE mark attached) DECLARATION OF CONFORMITY Network Compatibility Declaration We declare under our sole responsibility that this Manufacturer’s Name: Caddx Controls product is designed to work with the networks in Manufacturer’s Address: 1420 N. Main Street the countries marked with a check ( ) and may Gladewater, TX have interworking problems with the countries that...
LOCAL TELEPHONE COMPANY INTERFACE INFORMATION TELEPHONE CONNECTION REQUIREMENTS Except for telephone company provided ringers, all connections to the telephone network shall be made through standard plugs and standard telephone company provided jacks or equivalent in such a manner as to allow for immediate disconnection of the terminal equipment. Standard jacks shall be so arranged that if the plug connected thereto is withdrawn, no interference to the operation of the equipment at the customers premises which remains connected to the telephone network, shall occur by reason of such withdrawal.
UNDERWRITERS LABORATORIES INFORMATION The NetworX NX-4 holds the following listings from Underwriters Laboratories (US and Canada): Household Burglary (UL1023) (ORD-C1023-1974) Household Fire (UL985) (CAN/ULC S545-M89) Local Grade A Mercantile, Police Station Connect with Basic Line Security (UL609) (requires #NX-003-C enclosure) (CAN/ULC S303-M91) Grade B &...
SIA SYSTEM REQUIREMENTS (ANSI-SIA CP-01) To meet SIA CP-01 requirements – • Minimum System Requirements: 1 control panel; 2 keypads • Remote arming shall NOT be enabled in SIA classified installations. • Off-premise transmission must be in the SIA format. •...
1420 N. MAIN STREET GLADEWATER, TEXAS 75647 Main 800-727-2339 Technical Support 800-727-2339 Outside the US 903-845-6941 Tech Support Fax 903-845-8409 Main Fax 903-845-6811 Sales & Literature 800-547-2556 Web: www.caddx.com www.ge-security.com UL approved for ANSI/SIA NX-4 INSTALLATION MANUAL CP-01-2000 NX4IM04 REV. M (AUG 2004)