To avoid unneeded service calls, prevent possible injuries, and get the most out of your pump, READ THIS MANUAL CAREFULLY! The Sta-Rite ‘C’ and ‘CC’ Series Centrifugal pump: • Is designed for use with commercial swimming pools or as a centrifugal pump.
• Check all clamps, bolts, lids, and system accessories before testing. • Release all air in system before testing. • Tighten Sta-Rite trap lids to 25 ft. lbs. (3.5 kg-m) torque for testing. • Water pressure for test must be less than 25 PSI (7.5 kg/cm •...
UNCRATING AND INSPECTION Handle with care. Check items received against packing list to be sure that all equipment has been received. Inspect for shipping damage. If found, file claim with carrier immediately. Cleanup Clean up all trash and other materials which will interfere with installation from foundation and surrounding area.
Outlets Per Pump Provide at least two hydraulically balanced main drains, with covers (see above), for each swimming pool pump suction line. The centers of the main drains (suction fittings) must be at least three feet apart. The system must be built so that it cannot operate with the pump drawing water from only one main drain (that is, there must be at least two main drains connected to the pump whenever it is running).
Piping – Suction Risk of severe injury or drowning from hair or body entrapment. To reduce risk of entrapment against pump suction opening, connect pump to multiple drains and skimmers of non-entrapment design. See “Pool Pump Suction Requirements,” Pages 4 and 5. NOTICE: If pump suction becomes clogged, pump will cavitate, damaging pump internal parts.
ELECTRICAL Disconnect power at service panel before connecting motor. Ground motor before connecting to electrical power supply. Failure to ground motor can cause severe or fatal electrical shock hazard. Do not ground to a gas supply line. To avoid dangerous or fatal electrical shock, turn OFF power to motor before working on electrical connections.
Fire Hazard. Before using pump, check your motor nameplate for voltage. Your electric supply voltage and the stamped nameplate voltage must agree. Motors stamped 200 volts or 230 volts, must be used with that voltage only. Motors stamped with two voltages (for example 230/460 volts), may be used with either supply voltage.
OPERA TION Hazardous suction. Can trap hair or body parts, causing severe injury or death by drowning. Do not block pump or strainer Hazardous suction with body. Small children using pool must ALWAYS suction. have close adult supervision! Do not run pump against closed discharge valve. To do so can boil water in pump body, which cause pump to explode and can cause severe burns to people working on pump.
‘C’ and ‘CC’ SERIES COMMERCIAL Rotating Seat POOL PUMP DISASSEMBLY/ ASSEMBLY Spring See Exploded View, Page 14. Stationary Seat Shaft Seal Replacement NOTICE: The highly polished and lapped faces of the seal are easily dam- Figure 2 1419 1294 aged. Follow instructions and handle the seal with care. Be sure unit is grounded and power disconnected before If Gear Puller is used, attempting any work on pump or motor.
NOTICE: BE SURE you do not scratch seal face. 6. Dispose of cardboard washer and recheck seal face to be sure it is free of dirt, foreign particles, scratches and grease. 7. Inspect shaft and shaft sleeve to be sure they are clean. 8.
NOTICE: A clogged basket will cause cavitation, which will damage strainer basket, impeller, and pump. Clean weekly or each time you vacuum pool, whichever comes first. NOTICE: Basket is a close fit in body of strainer. When cleaning basket, do not deform.
TROUBLESHOOTING GUIDE Read symptom describing problem below at left. Causes for problems (bottom) are keyed to numbers at right. Check pump for causes listed at right and correct those that apply. Hazardous voltage. Can shock, burn or kill. SYMPTOM KEY NUMBERS FOR CAUSES Pump does not deliver liquid 1, 2, 3, 4, 6, 8, 10, 11, 14, 15, 16, 17 Pump delivers too little flow...
‘C’ / ‘CC’ Series Centrifugal Pumps 3 and 5 HP Medium and High Head 1904 0795 Model Number CCMH-136S CMH-136 CCHH-137S CHH-137 CCHJ-138 CHJ-138 CCMJ3-136S CMH3-136 CCHH3-137S CHH3-137 CCHJ3-138 CHJ3-138 CCM2H-136 CM2H-136 CCH2H-137 CH2H-137 CCH2J3-138 CH2J3-138 CCM2H3-136 CM2H3-136 CCH2H3-137 CH2H3-137 –...
The foregoing warranties relate to the original consumer pur- chaser (“Purchaser”) only. Sta-Rite shall have the option to re- HRPB, DEPB and System 3 – Tanks ... .10 years pair or replace the defective product, at its sole discre- Internal filter components and valves .