Single phase - .6/.8/1.0/1.2/1.5/2.0/2.4 kva, single phase - .6/.8/1.0/1.5 kva plus (41 pages)
Summary of Contents for Toshiba 1600XP SERIES
BATTERY CABINET 1600XP SERIES 8-22kVA BATTERY CABINET INSTALLATION AND OPERATION MANUAL SINGLE PHASE – 8/10/14/18/22 kVA: 288Vdc Part# 64024-002 August 2013...
1600XP Series Battery Cabinet Installation and Operation Manual...
1600XP SERIES 8-22kVA BATTERY CABINET INSTALLATION AND OPERATION MANUAL SINGLE PHASE- 8/10/14/18/22 kVA: 288 Vdc Part# 64024-002 August 2013 1600XP Series Battery Cabinet Installation and Operation Manual...
BATTERY CABINET SYSTEM If additional information or technical assistance is required call Toshiba’s Customer Support Center toll free at 1-877-867-8773 or write to: Toshiba International Corporation, 13131 W. Little York Rd., Houston, TX 77041-9990. Please complete the following information for your records and keep this manual with the...
GENERAL SAFETY INSTRUCTIONS Warnings in this manual appear in any of four ways: Danger- The danger symbol is a lightning bolt mark enclosed in a triangle which precedes the 3/16-inch high letters spelling the word “DANGER”. The danger symbol is used to indicate imminently hazardous situations, locations, and conditions which, if not avoided, WILL result in death, serious injury, and/or severe property damage.
Misuse of this equipment could result in human injury and equipment CAUTION damage. In no event will Toshiba Corporation be responsible or liable for either indirect or consequential damage or injury that may result from the misuse of this equipment.
IMPORTANT BATTERY SAFETY INSTRUCTIONS Proper maintenance to the battery system of this unit must be done by a WARNING qualified service technician. This is essential to the safety and reliability of your UPS system. Refer to service manual. A battery can present a risk of electrical shock and high short DANGER circuit current.
INSTRUCTIONS IMPORTANTES CONCERNANT LA SÉCURITÉ Cette notice contient des CONSERVER CES INSTRUCTIONS instructions importantes concernant la sécurté Un battery puet présenter un risque de choc électrique, de brûlure ATTENTION par transfert d’ énergie. Por le replacement, utiliser le même nombre de batteries du modéle ATTENTION suivant.
It is illegal to dump lead-acid batteries in landfills or dispose of improperly. Please help our Earth by contacting the environmental protection agencies in your area, the battery manufacturer, or call Toshiba toll-free at (877) 867-8773 for more information about recycling.
This will result in damage to the UPS, the Battery System, or both. Call your Toshiba representative if you should have any questions. 2) Before connecting the Battery System to the UPS; switch the ON/OFF switch MCCB2, located on the rear panel of the battery system to the OFF position.
4. Connect cabinet 2 CN14A to cabinet 1 CN24. Battery Cabinet Cabling The battery cabinets ship with six-foot long connection cables. Contact Toshiba Customer Support at 1-877-867-8773 if longer cables are required for your application, or if additional cables or connectors are required.
Connection Instructions and Diagrams 14/18/22 kVA Battery Connections The following illustration shows the wiring connections between the UPS and the battery cabinet. DANGER Contacts are not rated with interrupting capacity. Ensure the MCCB switch on the rear panel of the Battery Unit is set to the OFF position before connecting the UPS to the battery cabinet.
Connection Instructions and Diagrams 8/10 kVA Battery Connections The following illustration shows the wiring connections between the UPS and the Battery Unit. DANGER Contacts are not rated with interrupting capacity. Ensure the MCCB switch on the rear panel of the Battery Unit is set to the OFF position before connecting the UPS to the battery cabinet.
Preventive and Scheduled Maintenance / Part Replacement Preventive Maintenance Toshiba's 1600XP Series of UPS battery cabinets have been designed to provide years of trouble-free operation requiring a minimum of preventive maintenance. The best preventive measure that the battery cabinet user can take is to keep the area around the unit, particularly the air inlet vents, clean and free of moisture and dust accumulations.
Power Cables The three battery cabinet connector cables (battery positive, battery negative, and battery charger) are each equipped with individually keyed Anderson connectors to prevent cross connecting the battery cabinet and UPS circuitry. The battery cabinet connector cables are six (6) foot in length. Emergency Power Off (EPO) EPO Cabling The Battery Cabinet does not have an EPO.
1600XP System Backup Runtime The following runtime table gives the approximate combined backup runtimes at different load levels for 1600XP UPS models equipped with one and two battery cabinets. NOTE: These values are approximate and are dependent on many variables including operating environment, age of the batteries, battery temperature, and discharge history.
1600XP 8-22kVA Battery Cabinet Installation and Operation Manual...
INDUSTRIAL DIVISION 13131 West Little York Rd., Houston, TX 77041 Tel: 713/466-0277 Fax 713/466-8773 US 877/867-8773 Canada 800/872-2192 Mexico 01/800/527-1204 www.toshiba.com/ind Printed in the U.S.A.