1600XP Series Single Phase Uninterruptible Power Systems
Product Specifications – Rev 5.0 October 2013
3.6kVA – 22kVA
This specification document describes the Toshiba 1600XP Series. The 1600XP is continuous
duty, single-phase, on-line, solid-state uninterruptible power supply system hereafter referred to
as the UPS. The UPS will supply a clean regulated AC power output sine wave which is
unaffected by the quality of the AC input. The input and output voltages are single phase.
2.0 General Operation
Under normal operating conditions, the UPS' rectifier converts alternating current AC power to
direct current (DC) power, which is required for the system's inverter and battery charger. The
charger supplies regulated DC power to keep the batteries constantly charged. The inverter uses
pulse width modulation (PWM) that fully utilizes the characteristics of insulated-gate bipolar
transistors (IGBT) to convert DC power to regulated AC power. Therefore there is a constant
supply of power. The batteries will instantaneously supply the inverter DC power when on AC
power line failure occurs.
The UPS is designed in accordance with and is compliant with the following sections of the
current revisions of the following standards:
- ANSI C62.41 (IEEE 587) – Standard for Surge Withstand ability
- UL 1778 (CUL)
- FCC Class A
- National Electrical Code (NFPA-70)
- NEMA PE-1
- ISO 9001, 14001
All materials used are of new manufacture using the latest technology and have not been in prior
service except for specified factory testing. IGBT's are used exclusively in the rectifier inverter
and chopper sections.
All functioning components are solid state with no moving parts.
The UPS consist of the following components:
A. Rectifier Converter
B. Chopper / Charger
C. Pulse-Width Modulated (PWM) Inverter
D. Static Switch Bypass