Gas and Electric
3-prong ground-type outlet
should be located on left hand
side of cutout 8" (20.3 cm)
max. from enclosure sidewall.
10" (25.4 cm)
Gas and Electric
product rating/serial tag
with product) must be
installed with arrow up
pointing at cooktop
AGA or CSA approved
steel gas supply line
Typical Gas and Electric
Gas supply line should be
located in this area on rear or
side walls, or the supply line can
come up through the floor.
control support panel
36" (91.4 cm)
power supply cord
shut off valve
Copies of the standards listed may be
* CSA International
8501 East Pleasant Valley Rd.
Cleveland, Ohio 44131-5575
Note: Solid side and
bottom of cutout
enclosure not shown.
Observe all governing codes and
Important: Cooktop must be connected
to a regulated gas supply.
local codes and ordinances. In the
absence of local codes, installations must
conform with American National
Standard, National Fuel Gas Code
ANSI Z223.1 — latest edition or
CANI — B149.1 or 2*.
model/serial rating plate are for elevations
up to 2,000 feet (610 m). For elevations
above 2,000 feet (610 m), ratings are
reduced at a rate of 4% for each 1,000
feet (305 m) above sea level.
with NATURAL gas. It is design-certified
by International Approval Services (I.A.S.)
for NATURAL and L.P. gases with
appropriate conversion. The model/serial
rating plate, located on the underside of
the burner box, has information on the
type of gas that can be used. If this
information does not agree with the type
of gas available, check with the local gas
Use a new AGA or CSA approved
gas supply line.
Install a shut-off valve.
Securely tighten all gas
If connected to LP, have a
qualified person make sure gas
pressure does not exceed 14"
Examples of a qualified person
include licensed heating
personnel, authorized gas
company personnel, and
authorized service personnel.
Failure to do so can result in
death, explosion, or fire.
This installation must conform with
Input ratings shown on the
The cooktop is equipped for use