All units feature a Service Button, Status LED, Power LED,
and two additional LEDs (T1 and R1) for commissioning
and troubleshooting. See also Table 7 and Table 8 and
Check if the Status LED's behavior is changed if you switch
the power OFF/ON. Please contact Honeywell if this does
not solve the problem.
Terminal Protection Cover; required for wall mounting. Bulk
pack set of ten covers.
▪ For large controllers, order no.: IRM-RLC
▪ For small controllers, order no.: IRM-RSC
Approvals and Certifications
▪ UL 60730-1, Standard for Automatic Electric Controls
for Household and Similar Use, Part 1: General
▪ CAN/CSA-E60730-1:02, Standard for Automatic
Electrical Controls for Household and Similar Use, Part
1: General Requirements;
▪ Complementary listing for UL916, CSA C22.2 No. 205;
▪ BTL-listed, BACnet ASC profile;
▪ FCC part 15B-compliant: This equipment has been
tested and found to comply with the limits for a Class B
digital device, pursuant to part 15 of the FCC Rules.
These limits are designed to provide reasonable
protection against harmful interference in a residential
installation. This equipment generates, uses, and can
radiate radio-frequency energy and, if not installed and
used in accordance with the instructions, may cause
harmful interference to radio communications. However,
there is no guarantee that interference will not occur in a
particular installation. If this equipment does cause
harmful interference to radio or television reception,
which can be determined by turning the equipment OFF
and ON, the user is encouraged to try to correct the
interference by one or more of the following measures:
- Reorient or relocate the receiving antenna.
- Increase the separation between the equipment and
- Connect the equipment into an outlet on a circuit
different from that to which the receiver is connected.
- Consult the dealer or an experienced radio/TV
technician for help.
▪ RoHS Conformity.
SPYDER MODEL 5 ROOM CONTROLLERS − INSTALLATION GUIDE
Classification according to EN 60730-1
EN 60730 sub part:
Environmental conditions: For use in home (residential,
Rated impulse voltage:
Protection against shock: Class 0 (without terminal
Classification according to EN 60529
(Degree of protection provided by enclosures)
IP20. In the case of controllers mounted outside of a
cabinet, before applying power to the device, Terminal
Protection Covers (10-pc. bulk packs, order no.: IRM-RLC
for large housings and IRM-RSC for small housings) must
be mounted so as to provide IP30.
Ambient Environmental Limits
24 VAC Models (5to90% r.H., non-condensing)
31-00281ES-01 (EN1B-0664GE51 R0819)
commercial, and light-
control, for panel-mounting
500 V at 24 V
Class II (with terminal covers)
32 to 122 °F (0 to +50 °C)
-4 to +158 °F (-20 to +70 °C)