ALL THE SERVICE ALARMS GENERATED FOR APPLIANCE FAULTS ARE SIGNALLED ON THE DISPLAY THROUGH
THE ASSISTANCE REQUEST ICON
BE FAULT ALARM
FAULT ALARM (IF PRESENT)
CLEAN ALARM (ACTIVA-
TABLE IF CONDENSER PRO-
BE IS PRESENT)
LED LIGHT CE ALARM
(in Premium models only)
From ser. no.:
SERVICE ALARMS AND SIGNALLING
In case of faulty thermostatting probe, the display shows the messa-
ge rE alternating with E0 (compartment probe S1). The appliance still
works and compressor activation and/or deactivation is time mana-
ged (15 min. ON and 15 min. OFF). The alarm condition is automati-
cally reset as soon as compartment probe operation is restored.
In case of faulty room probe, the display shows the message E1 (room
probe S2). The alarm condition is automatically reset as soon as com-
partment probe operation is restored.
The service alarm signalling icon ﬂ ashes whereas the controller buzzer
The service alarm signalling icon ﬂ ashes whereas the controller buz-
zer is deactivated. In case of faulty condenser probe (if installed on
the machine), the display alternately shows the message SEr/E2. The
alarm condition is automatically reset as soon as compartment probe
operation is restored.
alarm: when the condenser is very dirty on the display will
appear the label CLn; this alarm dosen't stop the cycle but only
advises the customer to clean the condenser. The
appears only after 90 days to work of compressor and when the
temperature of the condenser and ambient is over to delta of the
The alarm disapears when the temperature decrease from parameter
ACd.( differential) or pressing the button Prg.
With the LED lamp disconnected, the display will show the message
ce in sequence of temperature.
This happens when the lamp is disconnected or damaged.
In case of no lamp connection, the controller does not diagnose any fault.
The alarm disappears when the lamp is reconnected.
Parameter to be conﬁ gured for lamp A9=9