WARNINGS AND CAUTIONS
Always strictly observe the "UPS Safety Rules"
Check carefully the integrity of the equipment.
In case you note some visible damage, do not install the equipment but contact the nearest Service
WARNING: RISK OF ELECTRICAL SHOCK.
Do not remove any UPS covers; there are no user serviceable parts inside.
After switching off, it takes up to 5 minutes for the DC capacitors to discharge because a lethally
high voltage remains at the terminals of the electrolytic capacitors.
All maintenance and service work should be performed by qualified service personnel.
The outlet-bars may be electrically live, even when the UPS is disconnected from the mains.
Store the SNMP/Web adapters in a dry location; storage temperature must be within -25°C to 55°C
(-13°F to 131°F).
The SNMP/Web adapters are ESD sensitive devices. When handling the adapters, only touch the
front panel / external cover and use suitable ESD protection (e.g. wrist straps).
The SNMP/Web adapters contain a removable, lithium coin-cell battery.
Perchlorate Material - special handling may apply.
Switching OFF the unit does not isolate the UPS from the mains.
Do not install the equipment in an excessively humid environment or near water.
Avoid spilling liquids on or dropping any foreign object onto the equipment.
The equipment should be placed in a sufficiently ventilated area; the ambient temperature should
not exceed 35°C (95°F).
The SNMP/Web adapters contain a removable, lithium coin-cell battery. The battery has been
selected in order to power to the relevant devices for over 10 years, therefore battery replacement
should not be necessary and it is not recommended. In any case, replace only with batteries of the
same type, and properly dispose or recycle used batteries.
Never dispose of battery in a fire: they may explode.
Do not try to open or mutilate battery: their contents may be toxic.
Never short-circuit the battery.
Installation Guide SNMP/Web Adapter