Loosen the screws on terminal block and insert the wires fully into terminal
block, then tighten the screws.
If wiring is not correct, the unit will not operate properly and it could cause a
defect in the unit.
Fix the cable with a clamp.
If the drain-elbow is used,
please attach as shown in figure.
(Note: Only for heat pump unit.)
Purging Method:To use vacuum pump
Detach the service port's cap of
and 3-way valve. Connect the service port to the low side of the gauge manifold
and connect the vacuum pump to the center port of the manifold.
Open the handle on the low side of the gauge manifold and operate vacuum pump.
Vacuum the tubing for at least 15 minutes. The vacuum level on the low side gauge
should be 29.9 in of Hg, 76 cm of Hg, 0.1 MPa. when vacuuming is complete, close
the valve on the manifold and turn off the vacuum pump. The vacuum level should
hold for 1-2 minutes. If the vacuum level does not hold, check the flared connections
and repeat this step.
Open the 2-way valve 1/4 turn. After 5-6 seconds, close the valve and inspect for
leaks with a leak detector or soap solution.
No gas leakage? Go to step 6.
In case of a leak, try tightening the flare connections to fix the leak. If the
leak stops, go to step 6. If the leak continues, check the flare connections
and repair as needed, then go back to step 3. then proceed step 6. If leak
continues, remove the refrigerant used for the leakage check and flare
tubes again. Repeat vacuum and leak and if no leakage, proceed to step 6.
from the service port, open 2-way valve and 3-way
Detach the charge hose
To prevent the gas leakage,
After attaching the caps, check for leakage around the caps.
2-way valve Liquid Side
3-way valve Gas Side
2-way valve 3-way valve
If the refrigerant of the air conditioner leaks, it is necessary to discharge all the
refrigerant. Repair the leak, vacuum the unit then charge the liquid refrigerant
into air conditioner
according to the amount marked on the name plate.
Please do not let other cooling medium, except speciﬁed one (R410A), or air
enter into the cooling circulation system. This could cause high pressure and
could cause a leak and lead to personal injuries.
3-way valve, and the valve cap for 2-way valve
replace the service port and valve caps.
Service port cap
Power Source Installation
The power source must be exclusively used for air conditioner.
In the case of installing an air conditioner in a moist place, please install an ea-
rth leakage breaker.(GFCI)
For installation in other places, use an HVACR circuit breaker of time delay fuse.
Please install the drain hose and ensure downward flow.
Please don't do the drainage as shown below.
The end is imm-
ersed in water.
Please pour water in the drain pan of the indoor unit, and
In case that the attached drain hose is in a room, please apply insulation to
to the hose to prevent condensation.
Refrigerant charge label
Contains fluorinated greenhouse gases
covered by the Kyoto Protocol
This product contains fluorinated greenhouse gases covered by
the Kyoto Protocol. Do not vent into the atmosphere.
GWP=global warming potential
Please fill in with indelible ink,
the factory refrigerant charge of the product
the additional refrigerant amount charged in the field and
• 1+2 the total refrigerant charge
on the refrigerant charge label supplied with the product.
The filled out label must be adhered in the proximity of the product
charging port (e.g. onto the inside of the stop value cover).
A contains fluorinated greenhouse gases covered by the Kyoto
B factory refrigerant charge of the product: see unit name plate
C additional refrigerant amount charged in the field
D total refrigerant charge
E outdoor unit
F refrigerant cylinder and manifold for charging
Check for Installation and Test Run
Please kindly explain to our customers how to operate
through the instruction manual.
Check Items for Test Run
Gas leak from interconnecting tubing?
Installation is on the interconnecting tubing?
Are the connecting wirings of indoor and outdoor ﬁrmly
inserted to the terminal block?
Is the connecting wiring of indoor and outdoor ﬁrmly ﬁxed?
Is drainage securely carried out?
Is the ground wire securely connected?
Is the indoor unit securely ﬁxed?
Is power source voltage the local codes?
Is there any noise?
Are the lights near the unit working normally?
Are cooling and heating (when in heat pump) performing normally?
Is the operation of room temperature control normal?
The gap with the
There is the bad
ground is too small.
smell from a ditch
conﬁrm that drainage
Put check mark