Power Supply Cable Installation
1. For direct wire installations, run the home power supply cable
according to the National Electric Code or CSA standards
and local codes and ordinances. There must be enough
wiring from the fused disconnect (or circuit breaker) box to
make the connection in the hood electrical terminal box.
For optional power supply cord kit installations, follow the
instructions in the "Make Electrical Connection" section.
NOTE: Do not reconnect power until the installation is
2. Remove the screw from the terminal box cover. Remove
terminal box cover and set aside.
A. Terminal box cover
3. Remove the power supply knockout from the top or rear of
the vent hood (depending on the incoming location of your
home power supply cable), and install a UL listed or CSA
" strain relief.
A. Power supply knockout
4. Using 2 or more people, lift the hood into final position. Feed
enough electrical wire through the ½" UL listed or CSA
approved strain relief to make connections in the terminal
box. Tighten the strain relief screws.
5. Position the range hood so that the large end of the keyhole
slots are over the mounting screws. Then push the hood
toward the wall so that the screws are in the neck of the slots.
Tighten the mounting screws, making sure the screws are in
the narrow neck of slots.
6. Connect ventwork to hood. Seal joints with vent clamps or
duct tape to make secure and airtight.
7. Check that back draft dampers work properly.
1. Disconnect power.
2. Use UL listed wire connectors and connect white wires (A)
3. Use UL listed wire connectors and connect black wires (B)
4. Connect green (or bare) ground wire from power supply to
5. Install terminal box cover.
6. Reconnect power.
Make Electrical Connection
Electrical Shock Hazard
Disconnect power before servicing.
Replace all parts and panels before operating.
Failure to do so can result in death or electrical shock.
A. White wires
B. Black wires
C. UL listed wire connector
D. Green (or bare) ground wire
Electrically ground the blower.
Use copper wire.
Connect ground wire to green ground screw in
Failure to do so can result in death, fire, or
green ground screw in terminal box and securely tighten.
E. Home power supply cable or
power cord accessory kit
F. UL listed or CSA approved
½" strain relief
G. Green ground screw