5 Installation and commissioning
5.1 Mechanical installation
Fit the unit in an aperture 28.5 x 70.5 mm and secure it with the
relevant mounting frame
a) housings with terminal box cover plate
(max. thickness 22 mm):
b) housings without terminal box cover plate
(max. wall thickness 18 mm):
For walls thicker than 10 mm: remove side plastic spacers from the
For the final fixing at the unit side screws have to be tightened
Use a cable clamp to secure sensor T1 in a suitable position.
Secure evaporator sensor T2 in the evaporator fin core at the point
where it is suspected icing is the greatest. It is advisable to use a
point in the lower third of the finned evaporator.
Fit onto back panel of electrics cabinet using the side mounting
holes and screws with a max. diameter of 3.5 mm.