INSTALLATION 10. On units with a by-pass, place in bypass position. Turn on the main water supply. Open a cold soft water tap nearby and let run a few minutes or until the system is free from Water Pressure foreign material (usually solder) that may have resulted A minimum of 20 pounds (1.4 bar) of water pressure is from the installation.
STARTUP INSTRUCTIONS CONTINUED Setting the Time of Day 1. Press and hold either the Up or Down buttons until the 5. Position the valve to the start of the brine tank fill cycle. programming icon replaces the service icon and the Ensure water goes into the brine tank at the desired parameter display reads TD.
TIMER OPERATION Manually Initiating a Regeneration 1. When timer is in service, press the Extra Cycle button for 5 Meter Immediate Control seconds on the main screen. A meter immediate control measures water usage and 2. The timer advances to Regeneration Cycle Step #1 (rapid regenerates the system as soon as the calculated system rinse), and begins programmed time count down.
MASTER PROGRAMMING MODE CHART Before entering Master Programming, please contact your local professional water dealer. To enter CAUTION Master Programming, set time to 12:01 PM. Master Programming Options Abbreviation Parameter Option Options Abbreviation Gallons Display Format Liters dF1b Downflow/Upflow Single Backwash dF2b Downflow Double Backwash Fltr...
MASTER PROGRAMMING MODE 2. Valve Type (Display Code VT) Press the Extra Cycle button. Use this display to set the Valve When the Master Programming Mode is entered, all available Type. The Valve Type setting specifies the type of cycle that the option setting displays may be viewed and set as needed.
MASTER PROGRAMMING MODE CONTINUED 9. Safety Factor (Display Code SF) Press the Extra Cycle button. Use this display to set the Safety 5. Tank in Service (Display Code TS) Factor. This setting specifies what percentage of the system Press the Extra Cycle button. Use this display to set whether capacity will be held as a reserve.
MASTER PROGRAMMING MODE CONTINUED 16. Flow Meter Type (Display Code FM) Press the Extra Cycle button. Use this display to set the type 13. Regeneration Cycle Step Times of flow meter connected to the control. This option setting is Press the Extra Cycle button. Use this display to set the identified by “FM”...
USER PROGRAMMING MODE 6. Press the Extra Cycle button. Use this display to set the Current Day of the Week. This option setting is identified by “CD” in the upper left hand corner of the screen. User Programming Mode Options Abbreviation Parameter Description...
DIAGNOSTIC PROGRAMMING MODE CONTINUED 4. Press the Up button. Use this display to view the Hours in Service since the last regeneration cycle. This option setting is identified by “HR” in the upper left hand corner of the screen. 5. Press the Up button. Use this display to view the Volume Used since the last regeneration cycle.
TROUBLESHOOTING Problem Cause Correction Water conditioner fails to Electrical service to unit has been Assure permanent electrical service (check fuse, regenerate. interrupted plug, pull chain, or switch) Timer is defective. Replace timer. Power failure. Reset time of day. Hard water. By-pass valve is open.
TROUBLESHOOTING CONTINUED Error Codes NOTE: Error codes appear on the In Service display. Error Error Type Cause Reset and Recovery Code Cam Sense The valve drive took longer Unplug the unit and examine the powerhead. Verify that all cam Error than 6 minutes to advance to switches are connected to the circuit board and functioning the next regeneration position...
WATER CONDITIONER FLOW DIAGRAMS Single Backwash Positions Double Backwash Positions Black Cycle Cam Blue Cycle Cam Second Backwash Position (Double Backwash Units Only) (Part Number 17438) (Part Number 40609) Service Position Service Position 1. Backwash Position 1. First Backwash Position 2.
SERVICE INSTRUCTIONS Timer Replacement To replace timer refer to Replacing Brine Valve, Injectors and Replacing Brine Valve, Injectors and Screen Screen, steps 1–3. 1. Turn off water supply to conditioner: 1. Remove the control valve back cover. Remove the control If the conditioner installation has a “three valve”...
SERVICE INSTRUCTIONS CONTINUED Seal and Spacer Replacement To replace seals and spacers, refer to Replacing Brine Valve, Injectors and Screen, steps 1–3. 1. Remove the control valve back cover. Remove the control valve front cover. Disconnect the meter dome signal wire from the front cover and feed it back through the control.
SERVICE ASSEMBLIES Air Check Meter 60002-34 .....Air Check #500 34-inch 60626 ......5600SXT Meter Assembly Brine Line Flow Controls Piston Assembly 60022-12 .....BLFC .125 gpm 60102-71 .....5600SXT Piston Assembly, Downflow 60022-25 .....BLFC .25 gpm 60022-50 .....BLFC .50 gpm Safety Brine Valves 60022-100 ....BLFC 1.0 gpm 60027-FFA ....Safety Brine Valve Body 2300 Fitting Facing Arm...
For a detailed list of where Pentair trademarks are registered, please visit waterpurification.pentair.com/brands. § Pentair trademarks and logos are owned by Pentair plc or its affiliates. Third party registered and unregistered trademarks and logos are the property of their respective owners.