Hv uninterruptible power supply for ibm system x (13 pages)
Summary of Contents for Lenovo RT1.5kVA
2U Rack or Tower UPS RT1.5kVA,RT2.2kVA, and RT3.0kVA Installation and User's Guide...
2U Rack or Tower UPS RT1.5kVA,RT2.2kVA, and RT3.0kVA Installation and User's Guide...
Note Before using this information and the product it supports, read the general information in the Notices section; and read the Safety Information and the Environmental Notices and User Guide on the Lenovo Documentation CD that came with your product.
This section contains information for trained service technicians. Inspecting for unsafe conditions Use this information to help you identify potential unsafe conditions in a Lenovo product that you are working on. Each Lenovo product, as it was designed and manufactured, has required safety items to protect users and service technicians from injury.
Make sure that the insulation is not frayed or worn. 4. Remove the cover. 5. Check for any obvious non-Lenovo alterations. Use good judgment as to the safety of any non-Lenovo alterations. 6. Check inside the system for any obvious unsafe conditions, such as metal filings, contamination, water or other liquid, or signs of fire or smoke damage.
v Never assume that power has been disconnected from a circuit. Check it to make sure that it has been disconnected. v If you have to work on equipment that has exposed electrical circuits, observe the following precautions: – Make sure that another person who is familiar with the power-off controls is near you and is available to turn off the power if necessary.
L001 DANGER Hazardous voltage, current, or energy levels are present inside any component that has this label attached. Do not open any cover or barrier that contains this label. (L001) Safety...
Electrical voltage and current from power, telephone, and communication cables are hazardous. To avoid a shock hazard: v If Lenovo supplied a power cord(s), connect power to this unit only with the Lenovo-provided power cord. Do not use the Lenovo-provided power cord for any other product.
Exchange only with the Lenovo-approved part. Recycle or discard the battery as instructed by local regulations. In the United States, Lenovo has a process for the collection of this battery. For information, call 1-800-426-4333. Have the Lenovo part number for the battery unit available when you call.
R001 Important: The following general safety information should be used for all rack-mounted devices: DANGER Observe the following precautions when working on or around your IT rack system: v Heavy equipment—personal injury or equipment damage might result if mishandled. v Always lower the leveling pads on the rack cabinet. v Always install stabilizer brackets on the rack cabinet.
CAUTION: v Do not install a unit in a rack where the internal rack ambient temperatures will exceed the manufacturer’s recommended ambient temperature for all your rack-mounted devices. v Do not install a unit in a rack where the air flow is compromised. Ensure that air flow is not blocked or reduced on any side, front, or back of a unit used for air flow through the unit.
The upstream circuit breaker for Normal AC and Bypass AC must be easily accessible. The unit can be disconnected from AC power source by opening this circuit breaker. This circuit breaker is used for backfeed protection and must comply with IEC/EN 62040-1 (the creepage and clearance distances shall meet the basic insulation requirements for pollution degree 2).
Before installing your equipment, read the safety instructions. Then, follow the instructions in this manual for setting up and using the product. To discover the entire range of Lenovo products and the options available for the Lenovo UPS device, we invite you to visit our website or contact your Lenovo representative.
CD. End of life Lenovo will process products at the end of their service life in compliance with local regulations. Lenovo works with companies in charge of collecting and eliminating our products at the end of their service life.
The battery pack can be removed to comply with regulations and in view of correct disposal. With the Lenovo UPS device, you can eliminate the effects of power disturbances and guard the integrity of your equipment. Providing outstanding performance and reliability, the Lenovo UPS device's unique benefits include: v True online double-conversion technology with high power density, utility frequency independence, and power generator compatibility.
The kit is available from Lenovo. Refer to the instructions in the kit to install the brackets properly. The brackets are not required when the UPS and EBMs are installed in a pre-positioned rack.
Figure 2. Rack position Dimensions (mm/inch) D x Machine types and models Weights (kg/lb) W x H 5594-1KX 27.60 / 60.90 522 x 441.2 x 86.2 / 20.6 x 17.4 x 3.4 5594-2KX 28.50 / 62.80 5594-3KX 38.08 / 84.00 647 x 441.2 x 86.2 / 25.5 x 17.4 x 3.4 5594-2BX...
Rear panels: 100V/120V models USB communication port RS232 communication port Connector for automatic recognition of an additional battery pack Slot where UPS Network Management Card is installed Figure 3. 5594-1AX Connector for Remote On/Off (ROO) control or Remote Power Off (RPO) control Connector for additional battery pack...
Rear panels: 200V/230V models USB communication port RS232 communication port Connector for automatic recognition of battery packs Slot where UPS Network Figure 7. 5594-1KX Management Card is installed Connector for Remote On/Off (ROO) control or Remote Power Off (RPO) control Connector for battery packs 16A outlet for connection of equipment (Primary outlet group)
The following table shows the indicator status and description: Indicator Status Description Green The UPS is operating normally. Yellow The UPS is on Battery mode. The UPS has an active alarm or fault. See Chapter 7, “Troubleshooting and maintenance,” on page 35 for additional information.
The following table describes the status information provided by the UPS. Note: If another indicator appears, see Chapter 7, “Troubleshooting and maintenance,” on page 35 for additional information. Operation status Cause Description The UPS is OFF, waiting for Equipment is not powered Standby mode start-up command from the until...
Operation status Cause Description The UPS is on Battery mode This warning is approximate, End of backup time and the battery packs are and the actual time to shut running low. down might vary significantly. Depending on the UPS load and number of Extended Battery Modules (EBMs), the Battery LED is blinking...
User settings The following table displays the options that can be changed by the user. Table 1. User settings Submenu Available settings Default settings Local settings Language [language_name] [English] Select the desired User selectable when language from the UPS is powered for list.
Table 1. User settings (continued) Submenu Available settings Default settings In/Out settings Output voltage Low voltage: [100 V] Low Voltage model: [120 V] [125 V] 110 V High voltage: [200 V] High Voltage model: [208 V] [220 V] [230 230 V V] [240 V] User selectable when UPS is powered for...
Table 1. User settings (continued) Submenu Available settings Default settings In/Out settings Load segments - [No Delay] [1 s] [2 Outlet Group 1: [3 s] (continued) Auto start delay s]...[65354 s] Outlet Group 2: [6 s] The unit is powered on with the specified delay relative to the primary outlet group.
Table 1. User settings (continued) Submenu Available settings Default settings On/Off settings Cold start [Enabled] [Disabled] [Enabled] Authorize the unit to start on battery power. Forced reboot [Enabled] [Disabled] [Enabled] If mains recover during a shutdown sequence: If set to Enable, shutdown sequence will complete and wait 10 seconds prior...
Table 1. User settings (continued) Submenu Available settings Default settings Battery settings Automatic battery Every week (in [No test] [Every day] test constant charge) [Every week] [Every otherwise following month] Available only if battery charge mode is set to constant charge.
Unpacking and contents check: 200V/230V models About this task Lenovo UPS Mounting kit for 19-inch enclosures UPS Network Management Card ( 3AX and 3KX only) 2 connection cables for the protected equipment 2 cable locking systems R232 communication cable USB communication cable...
The UPS and connected EBMs must be installed no higher than 5 feet (1.5m) above the floor to allow for easy installation and servicing. Procedure For mounting on rails, follow steps 1 to 4 in the illustration. Note: The rails and necessary hardware are supplied by Lenovo. Chapter 3. Installation...
Tower installation Procedure 1. Attach tower supports as shown. 2. Adjust the orientation of the LCD panel and the logo, as shown. Installing the communication card About this task Note: It is not necessary to shut down the UPS before installing the UPS Network Management Card.
UPS connection: AX models About this task Note: Check that the indications on the name plate located on the back of the UPS correspond to the AC-power source and the true electrical consumption of the total load. Note: The UPS charges the battery packs as soon as it is connected to the AC-power source, even if the button is not pressed.
Note: The UPS charges the battery packs as soon as it is connected to the AC-power source, even if the button is not pressed. Procedure 1. Connect the UPS input socket to the AC-power source using the cable of the protected equipment. Connect a 250 V - 16 A cable to the socket , then to the AC-power source.
Figure 11. Unpacking the EBM Figure 12. Rack installation using rails Figure 13. Installing one EBM (rack) Figure 14. Installing four EBMs (rack) Chapter 3. Installation...
Figure 16. Installing four EBMs (tower) Figure 15. Installing one EBM (tower) Installation and User's Guide...
To start the UPS: Procedure 1. Verify that the UPS power cord is plugged in. 2. The UPS front panel display illuminates and shows the Lenovo logo. 3. Verify that the UPS status screen shows 4. Press the button on the UPS front panel for at least 3 seconds.
(unless the restart function has been disabled) and the load is supplied again. UPS remote control functions Lenovo UPS offers a choice between two remote control functions. Remote Power Off (RPO): allows a remote contact to be used to disconnect all the equipment connected to the UPS.
These functions are obtained by opening a contact connected between the appropriate pins of connector on the rear panel of the UPS (see the figures in “Remote control connection and test”). Remote control connection and test Procedure 1. Check that the UPS is OFF and disconnected from the AC input source -- for example, by turning off the utility power circuit breaker to which the UPS is attached.
Table 2. Operating modes (continued) High Mode Online Battery Standby Efficiency* Power failure Power sag Power surge Under voltage Over voltage Note: (*) High Efficiency mode introduces a delay between loss of input power and switching to battery power. Installation and User's Guide...
USB RS232 communication port on the UPS. Results The UPS can now communicate with Lenovo power management software. Characteristics of the contact communication port (optional) Pins 1, 3, 4, 5, 6, 10: not used Pin 2: common (user)
v Current: 25 mA max v Power: 1.2 W Replacing the communication card About this task Follow these steps to replace the UPS Network Management Card. 1. Turn off the UPS. 2. Disconnect the network cable. 3. Remove the connector panel blank ( which is secured by two screws.
Carry out the instructions in “Removing the battery pack” in reverse order. Note: To ensure safety and high performance, use only battery packs supplied by Lenovo. Important: Take care to firmly press together the two parts of the connector during remounting.
Structural parts: Purchase and replacement of structural parts (components such as the top cover) is your responsibility. If Lenovo acquires or installs a structural part at your request, you will be charged for the installation.
Table 3. Parts listing table: RT1500 VA and RT2200 VA models Part 5594- 5594- 5594- 5594- Description Type 1500 VA / 1350W 120V 2U Tier 1 00FP721 Rack (without batteries) 1500 VA / 1350W 230V 2U Tier 1 00FP722 Rack (without batteries) 2200 VA / 1980W 120V 2U Tier 1 00FP723...
Table 5. Parts listing table: Extended battery modules (continued) Description Type Part No. 5594-2BX 5594-3BX 5PX 2U Bezel (RT2U models) Tier 1 CRU 00FP803 Tower pedestal feet Tier 1 CRU 00FP825 Ship Bracket for 5PX Tier 1 CRU 00FP826 Chapter 8. Parts listing...
Appendix A. Specifications Technical specifications: 100V/120V models The Lenovo 2U Rack or Tower UPS, 100V model and 120V model, is a single-phase UPS unit. 5594-1AX 5594-2AX 5594-3AX Output Power 2880 VA - 2700 W 1440 VA 1950 VA 1440 W...
20 A, 250 V. This product is designed for IT power distribution systems. Technical specifications: 200V/230V models The Lenovo 2U Rack or Tower UPS, 200V model and 230V model, is a single-phase UPS unit. 5594-1KX...
Lenovo to assist you. Use this information to obtain additional information about Lenovo and Lenovo products, and determine what to do if you experience a problem with your Lenovo system or optional device. Note: This section includes references to IBM web sites and information about obtaining service.
The troubleshooting information or the diagnostic programs might tell you that you need additional or updated device drivers or other software. Lenovo maintains pages on the World Wide Web where you can get the latest technical information and download device drivers and updates.
In the U.S. and Canada, call 1-800-IBM-SERV (1-800-426-7378). Hardware service and support IBM is Lenovo's preferred service provider for the System x, Flex System and NeXtScale System products. You can receive hardware service through your Lenovo reseller or from IBM. To locate a reseller authorized by Lenovo to provide warranty service, go to http://www.ibm.com/partnerworld and click Business Partner Locator.
IBM Taiwan Corporation 3F, No 7, Song Ren Rd. Taipei, Taiwan Telephone: 0800-016-888 Installation and User's Guide...
(TBW). A device that has exceeded this limit might fail to respond to system-generated commands or might be incapable of being written to. Lenovo is not responsible for replacement of a device that has exceeded its maximum guaranteed number of program/erase cycles, as documented in the Official Published Specifications for the device.
Lenovo makes no representations or warranties with respect to non-Lenovo products. Support (if any) for the non-Lenovo products is provided by the third party, not Lenovo. Some software might differ from its retail version (if available) and might not include user manuals or all program functionality.
Properly shielded and grounded cables and connectors must be used in order to meet FCC emission limits. Lenovo is not responsible for any radio or television interference caused by using other than recommended cables and connectors or by unauthorized changes or modifications to this equipment.
EU-Mitgliedsstaaten und hält die Grenzwerte der EN 55022 Klasse A ein. Um dieses sicherzustellen, sind die Geräte wie in den Handbüchern beschrieben zu installieren und zu betreiben. Des Weiteren dürfen auch nur von der Lenovo empfohlene Kabel angeschlossen werden. Lenovo übernimmt keine Verantwortung für die Einhaltung der Schutzanforderungen, wenn das Produkt ohne Zustimmung...
Konformitätserklärung nach Paragraf 5 des EMVG ist die Lenovo (Deutschland) GmbH, Gropiusplatz 10, D-70563 Stuttgart. Informationen in Hinsicht EMVG Paragraf 4 Abs. (1) 4: Das Gerät erfüllt die Schutzanforderungen nach EN 55024 und EN 55022 Klasse A. Nach der EN 55022: „Dies ist eine Einrichtung der Klasse A. Diese Einrichtung kann im Wohnbereich Funkstörungen verursachen;...
Korea Communications Commission (KCC) statement This is electromagnetic wave compatibility equipment for business (Type A). Sellers and users need to pay attention to it. This is for any areas other than home. Russia Electromagnetic Interference (EMI) Class A statement People's Republic of China Class A electronic emission statement Taiwan Class A compliance statement Appendix C.
Advanced Battery Management (ABM) A three-stage charging system designed to prolong the service life of Lenovo UPS batteries. By charging the batteries only when necessary, battery life is significantly improved. Charging stage one: quickly recharges battery to approximately 90% of capacity. Charging stage two: fully charges the battery to 100%.