OWER VAILABILITY ™ ™ GXT2-6000RT230 & GXT2-4500RT230 ANUAL 230VAC...
ONFIGURATION ROGRAM GXT2-6000RT230 and GXT2-4500RT230 Configuration Program Features ... . 17 7.1.1 What You Will Need ............17...
Bypass Indicator LED (Amber) ..........19 UPS ON Indicator LED (Green) .
UPS performance alters in use. Refer all faults to your dealer. Only trained engineers authorized by Liebert should perform troubleshooting. To replace batteries, refer all servicing to qualified service personnel. Proper disposal of batteries is required. Refer to your local laws and regulations for disposal requirements.
LOSSARY YMBOLS Risk of electrical shock Indicates caution followed by important instructions AC input AC output Requests the user to consult the manual Indicates the unit contains a valve-regulated lead acid battery PbH2SO4 Recycle DC voltage Equipment grounding conductor Bonded to ground AC voltage ON/Alarm Silence/Battery Test OFF/Bypass...
The UPStation GXT2 has an interface port for communication between the UPS and a network server or other computer systems. This port provides detailed operating information including voltages, cur- rents, and alarm status to the host system when used in conjunction with Liebert MultiLink™ soft- ware. MultiLink software can also remotely control UPS operation.
YSTEM ESCRIPTION Input TVSS & EMI/RFI Filters Transient Voltage Surge Suppression (TVSS) and EMI/RFI Filters These UPS components provide surge protection and filter both electromagnetic interference (EMI) and radio frequency interference (RFI). They minimize any surges or interference present in the mains line and keep the sensitive equipment protected.
DC-to-DC Converter The DC to DC converter utilizes energy from the battery system and raises the DC voltage to the opti- mum operating voltage for the inverter. This allows the inverter to operate continuously at its opti- mum efficiency and voltage, thus increasing reliability. Battery The UPStation GXT2 utilizes valve-regulated, nonspillable, lead acid batteries.
AJOR OMPONENTS The GXT2 is composed of three major assemblies to provide easier handling, installation, and versa- tility. Main Frame and Electronics This 5U cabinet is shipped with internal batteries installed and a basic, hardwire distribution box attached and ready to install. Figure 1 GXT2, front view Top Trim...
Figure 2 GXT2, rear view Battery Disconnect External Battery Connector UPS Output Circuit Breaker DB-9 Communication Port Removable Power Distribution Box Internal Battery Packs The UPS has two internal battery packs behind a battery access door on the front of the unit. Each pack is fitted with a connector to link to the UPS.
Removable Power Distribution Box The UPS arrives with a basic hardwire power distribution pack installed. This box always contains the UPS input circuit breaker. Optional versions may be available to replace the standard box for custom installations. Power distribution boxes, basic, optional Figure 4 Basic Hardwire Power Distribution Box PD-CEHDWR...
’ NCLUDED The GXT2 are shipped with the following items: • GXT2-6000RT230 and GXT2-4500RT230 user manual • Vertical display overlay • Top bezels - 2 • MultiLink software CD • MultiLink serial cable, 10 ft (3m) • Rack mount handles •...
5.1.3 - Installing the Adjustable Rack-Mount Kit—Sold Separately shows the positioning of the rack-mounting brackets. Liebert recommends taking the internal batteries out of the UPS during rack installation. This will make the UPS cabinet lighter and easier to handle.
5.1.3 Installing the Adjustable Rack-Mount Kit—Sold Separately This kit contains parts needed to mount several different models of UPS and external battery cabi- nets into EIA310-D standard four-post racks that are 18-32" deep (457-813mm). The weight limit per pair of adjustable rack-mounting brackets is 91 kg (200lbs.). Parts included are: Item Rear bracket members...
Lifting equipment into the rack may be a two-person job, depending on the weight of the equipment. Liebert recommends taking the internal batteries out of the UPS during rack installation. This will make the UPS cabinet lighter and easier to handle.
Optional rack-mount handles are shipped with the external battery cabinet and may be installed at this time if desired. 3. Securing hardware and slide rails are sold separately. Please contact your local dealer or Liebert representative for these additional options and any assistance needed. Fasten the slides into position with the screws per the instructions included with the slide rails.
Connect the Internal Batteries Using the External Connector The internal connectors of the internal battery packs will be connected when shipped. However, the internal batteries will be disconnected from the UPS using a rear panel connector. The connector attaches to the UPS in both the open and closed position using two screws. The picture on the left shows the connector in the open position, as shipped.
Figure 6 Distribution box electrical connections diagram PD-CEHDWR Mains Input Input External Branch UPS - PFC, Battery, Inverter PD-CEHDWR and PD-CEHDWRBYP Terminal Block Connections Conduit entry holes are provided on the rear and side of the box. Input and output wiring should not share the same conduit.
NITIAL TART P AND 1. Verify that the Input Output circuit breakers are off. 2. During initial system checks, disconnect all loads (open load disconnects). 3. Inspect all wiring, cables, and connection. 4. If external battery cabinets are used, verify that the battery interconnect cables are fully inserted in the sockets.
UPS is put into full-time service powering the critical load. For most users operating with 230VAC and with no external batteries, the factory default settings will be adequate. GXT2-6000RT230 and GXT2-4500RT230 Configuration Program Features • Select one of three L-N output voltages to match local voltages. • Enable/Disable Auto-Restart.
• After 24 hours, retest the batteries. • After the batteries have been retested, if only three of the five Battery LEDs illuminate, contact your local dealer, Liebert representative or Liebert Worldwide Support Group. Standby/Manual Bypass Button This button controls output power to connected load(s) and has dual functions: Standby and Manual Bypass.
Load Level Indicators (4 Green, 1 Amber) The load level indicators display the approximate electrical load placed upon the UPS at all times. Battery Level Indicators (5 Green) The battery level indicators display approximate battery capacity at all times. The UPStation GXT2 is equipped with automatic and remote battery test features. The automatic test occurs every 14 days (this option is user configurable) if mains has not been interrupted.
PERATING NSTRUCTIONS Normal Mode Operation During normal operation, mains power provides energy to the UPS. The filters, power factor correction circuit and the inverter process this power to provide computer grade power to connected loads. The UPS maintains the batteries in a fully charged state. The four green load level LEDs indicate an approximate level of load in 25% increments.
2. 2. Pin 4 requires a 5-12 VDC signal to shutdown. This normally comes form the serial port using Liebert's contact closure cable. It cannot be used with just a contact closure unless the relay is used to switch a voltage source. A 5-12 VDC signal for 1.5 seconds or greater is required to signal a shutdown.
When the DB9 OCWEBCARD serial port cable is removed, the OCWEBCARD DB9 connector needs to be covered. The DB9 cover is included with the UPS. Liebert's MultiLink software continually monitors the UPS and can shut down your computer or server in the event of an extended power failure.
10.4 Remote Emergency Power Off The UPS is equipped with a Remote Emergency Power Off (REPO) connector. The user must supply a means of interfacing with the REPO circuit to allow disconnecting the UPS input feeder breaker to remove all sources of power to the UPS and connected equipment to comply with national and local wiring codes and regulations.
The UPStation GXT2 is designed to allow the user to safely replace the internal batteries. Read the safety cautions before proceeding. Contact your local dealer or Liebert representative to obtain the appropriate replacement battery kit part number and pricing.
• Do not lay tools or other metal objects on top of the batteries. • If the battery replacement kit is damaged in any way or shows signs of leakage, contact your local dealer or Liebert representative immediately. • Do not dispose of batteries in a fire. The batteries may explode.
11.2 AC Power Connections Power connections may be disconnected from the UPS cabinet via a removable distribution box. This may be a convenient feature if the UPS must be moved a short distance or replaced. This box allows power connections to be conveniently disconnection from the main UPS cabinet. A label is attached to the UPS to describe these procedures.
5 minutes while the battery charger is not operational. If a problem persists, consult your local dealer, Liebert representative or contact the Liebert World- wide Support Group. Please have the UPS model number and serial number available at the time of your inquiry.
Wait 30 minutes to allow UPS to cool, then restart UPS. If UPS does not restart, contact your local dealer, Liebert representative or the Liebert Worldwide Support Group. UPS requires service. Contact your local dealer, Liebert representative or the Liebert Worldwide Support Group.
UPS shuts down. UPS requires service. Contact your local dealer, Liebert representative or Liebert Worldwide Support Group. Check battery connections, completely power down and restart UPS.
Table 6 Battery run times Load% Internal Battery (minutes) 100% Internal Battery + 1 External Battery Cabinet (minutes) 100% Internal Battery + 2 External Battery Cabinets (minutes) 100% Internal Battery + 3 External Battery Cabinets (minutes) 100% Internal Battery + 4 External Battery Cabinets (minutes) 100% Using the configuration program, the user may specify the number of GXT2-240VBATT external bat-...
12.0.1 Auto-Learning Battery Run Times As batteries age, the estimated runtimes may become less accurate. The GXT2 is programmed to “learn” from a full battery discharge and modify the estimated runtime for the measured battery capacity. This can improve accuracy and compensate for aging batteries or batteries that operate at different ambient temperatures.
EN50091-2 and AS 62040-2: 2002, Class A; CE EMC Directive EN61000-4-2, Level 4, Criteria A EN61000-4-3, Level 3, Criteria A EN61000-4-4, Level 4, Criteria A EN61000-4-5, Level 3, Criteria A Specifications GXT2-4500RT230 4.5KVA / 3,150W 67 (151) 79.5 (175.3) 230VAC 220/230/240VAC 176 –...
Two IEC320 C19 16A/250V sockets Manual Bypass Switch with Indicator Lamps 32A, Supplied by User GXT2-240VBATT GXT2-6000RT230, GXT2-4500RT230 176 x 522 x 430 (6.9 x 20.55 x 16.9) 560 x 690 x 455 (22 x 27.2 x 17.9) 65 (145) 78.5 (173.1)
GXT2-6000RT230 The Company Behind the Products With over a million installations around the globe, Liebert is the world leader in computer protection systems. Since its founding in 1965, Liebert has developed a complete range of support and protection systems for sensitive electronics: •...